fw : monday evening ' s gas flow daren ,
the below memo was rec ' d on today from my contact at lyondell ( john allen )
referencing meter 98 - 1063 ' s gas pressure problems on last night ( 3 - 7 - 00 ) .
i thought that this might be some useful information to you .
thanks
- jackie -
3 - 9497
- - - - - - - - - - - - - - - - - - - - - - forwarded by jackie young / hou / ect on 03 / 07 / 2000 11 : 15
am - - - - - - - - - - - - - - - - - - - - - - - - - - -
" allen , john s . " on 03 / 07 / 2000 10 : 56 : 35 am
to : " ' young , jackie ' "
cc :
subject : fw : monday evening ' s gas flow
> - - - - - original message - - - - -
> from : john allen [ smtp : j _ s _ allen 77 @ hotmail . com ]
> sent : monday , march 06 , 2000 9 : 53 pm
> to : roger . maake @ lyondell - citgo . com
> cc : john . allen @ lyondell - citgo . com ; tony . cucinotta @ lyondell - citgo . com ;
> gmason @ noram . com ; david . rasco @ lyondell - citgo . com ;
> greg . wilson @ lyondell - citgo . com
> subject : monday evening ' s gas flow
>
> the natural gas pressure issue was attributed to 2 hpl values . the north
> one was not operative and the south one had leaking bellows .
> it was determined that an alternator supply for pressure contract was not
> readily available , being that it was after normal work hours .
>
> th hpl technician determined that he would be able to make repairs while
> the
> line was operative , and that it would not be necessary to request a
> shut - in
> condition . it would just take longer for him to make the repairs . the
> technician was able to control the pressure through the south valve while
> repairing the north valve .
>
> hpl agreed to the utilities department ' s request that the technician was
> not
> to leave lcr ' s facility this evening until such time as both valves were
> operative .
>
>
fw : monday evening ' s gas flow
daren ,
the below memo was rec ' d on today from my contact at lyondell ( john allen )
referencing meter 98 - 1063 ' s gas pressure problems on last night ( 3 - 7 - 00 ) .
i thought that this might be some useful information to you .
thanks
- jackie -
3 - 9497
- - - - - - - - - - - - - - - - - - - - - - forwarded by jackie young / hou / ect on 03 / 07 / 2000 11 : 15
am - - - - - - - - - - - - - - - - - - - - - - - - - - -
" allen , john s . " on 03 / 07 / 2000 10 : 56 : 35 am
to : " ' young , jackie ' "
cc :
subject : fw : monday evening ' s gas flow
> - - - - - original message - - - - -
> from : john allen [ smtp : j _ s _ allen 77 @ hotmail . com ]
> sent : monday , march 06 , 2000 9 : 53 pm
> to : roger . maake @ lyondell - citgo . com
> cc : john . allen @ lyondell - citgo . com ; tony . cucinotta @ lyondell - citgo . com ;
> gmason @ noram . com ; david . rasco @ lyondell - citgo . com ;
> greg . wilson @ lyondell - citgo . com
> subject : monday evening ' s gas flow
>
> the natural gas pressure issue was attributed to 2 hpl values . the north
> one was not operative and the south one had leaking bellows .
> it was determined that an alternator supply for pressure contract was not
> readily available , being that it was after normal work hours .
>
> th hpl technician determined that he would be able to make repairs while
> the
> line was operative , and that it would not be necessary to request a
> shut - in
> condition . it would just take longer for him to make the repairs . the
> technician was able to control the pressure through the south valve while
> repairing the north valve .
>
> hpl agreed to the utilities department ' s request that the technician was
> not
> to leave lcr ' s facility this evening until such time as both valves were
> operative .
>
>