Development of the CCP 200 mathematical model for Syzran CHPP using the Thermolib software package
Simplified cycle diagram of the CCP 200 power generating unit of Syzran CHPP containing two gas turbines PG6111FA with generators, two steam recovery boilers KUP 110/15 8.0/0.7 540/200, and one steam turbine Siemens SST 600 (one cylinder with two variable heat extraction units of 60/75 MW in heatextraction and condensing modes, accordingly) with S GEN5 100 generators was presented. Results of experimental guarantee tests of the CCP 200 steam gas unit are given. Brief description of the Thermolib application for the MatLab Simulink software package is given. Basic equations used in Thermolib for modeling thermo technical processes are given. Mathematical models of gas turbine plant, heat recovery steam generator, steam turbine and integrated plant for power generating unit CCP 200 of Syzran CHPP were developed with the help of MatLab Simulink and Thermolib. The simulation technique at different ambient temperature values was used in order to get characteristics of the developed mathematical model. Graphic comparison of some characteristics of the CCP 200 simulation model (gas temperature behind gas turbine, gas turbine and combined cycle plant capacity, high and low pressure steam consumption and feed water consumption for high and low pressure economizers) with actual characteristics of the steam gas unit received at experimental (field) guarantee tests at different ambient temperature are shown. It is shown that the chosen degrees of complexity, characteristics of the CCP 200 simulation model, developed by Thermolib, adequately correspond to the actual characteristics of the steam gas unit received at experimental (field) guarantee tests; this allows considering the developed mathematical model as adequate and acceptable it for further work.