New corrector system for the Fermilab Booster
We present an ambitious ongoing project to build and install a new corrector system in the Fermilab 8 GeV booster. The system consists of 48 corrector packages, each containing horizontal and vertical dipoles, normal and skew quadrupoles, and normal and skew sextupoles. Space limitations in the machine have motivated a unique design, which utilizes custom wound coils around a 12 pole laminated core. Each of the 288 discrete multipole elements in the system will have a dedicated power supply, the output current of which is controlled by an individual programmable ramp. This paper describes the physics considerations which drove the design, as well as issues in the control of the system.
Design and fabrication of a multi-element corrector magnet for the Fermilab Booster synchrotron
To better control the beam position, tune, and chromaticity in the Fermilab Booster synchrotron, a new package of six corrector elements has been designed, incorporating both normal and skew orientations of dipole, quadrupole, and sextupole magnets. The devices are under construction and installation at 48 locations is planned. The density of elements and the rapid slew rate have posed special challenges. The magnet construction is presented along with DC measurements of the magnetic field.
Heat Transfer Analysis in Cooling System of Hydropower’s Generator
Cooling process of power plant generator is handled via air-cooled radiators in which the cooling water is supplied from lake with its water temperature varies from season to season. In this study, the effect of temperature fluctuations of cooling water entering the cooling system has been examined via analysis of energy (NTU method) and exergy. The exergy analysis has been done by definition of efficiency coefficient for exergy of cooling media (water) and heating media (air). Besides, the effect of changing the cooling water temperature and flow rate entering the radiators on the cooling system performance has been studied. The results revealed the generator cooling system performance level held sufficient till the temperature of inlet water was kept under 293 k (20°C). On one hand, when the temperature of cooling water at the inlet rises to 12°C, the rate of heat exchange at radiators falls up to 34.3%. On the other hand, by water temperature passing the 12°C limit, the efficiency of cooling media exergy falls to 78% leading to efficiency rise in radiators’ heating media exergy level to 61%. According to the results of this study, changing flow rate of cooling media up to 40% gives rise to the efficiency coefficient of radiators’ cooling media exergy level to about 18.7%. While it does not affect the efficiency level of energy at radiators, the flow rate rise of cooling media may not be considered as a way to give rise to efficiency level of radiators.