Calculations for AP1000 nuclear power plant SGTR accident based on RELAP5/mod 3.3 program
AP1000 nuclear power plant model is founded via RELAP5/mod 3.3 program in detail. Refer to SGTR accident basic assumptions in the safety analysis report, calculations for AP1000 nuclear power plant SGTR accident are carried out. And through comparison between the result got and the result from safety analysis report calculated by LOFTTR2 program, the two results are very consistent. It's found that even if the operators do not interfere, AP1000 nuclear power plant protection systems and passive design measures will trigger an automatic response measures, it can terminate the SG heat transfer tube leaking and make RCS be stable in a safe condition and to prevent SG overflowing and ADS actions occurring.
Frequency and consequences associated with a steam generator tube rupture event
The results of a study into the frequency of steam generator tube rupture (SGTR) events are presented, including estimates on the upper and lower bound frequencies for U-tube and once-through steam generator plants and single- and multiple-tube ruptures. In addition, commercial pressurized water reactor operational data have been researched and iodine spiking data used to develop data bases of maximum resultant iodine concentrations and release rates. The frequencies and iodine spiking magnitudes are compared with other studies, and conclusions are drawn regarding current guidelines for analysis of this design-basis transient.
Fuel performance annual report for 1984. Volume 2
This annual report, the seventh in a series, provides a brief description of fuel performance during 1984 in commercial nuclear power plants. Brief summaries of fuel design changes, fuel surveillance programs, fuel operating experience, fuel problems, high-burnup fuel experience, and items of general significance are provided. References to additional, more detailed information and related NRC evaluations are included. 279 refs., 11 figs., 29 tabs.