A fifty megawatt klystron for the Stanford Linear Collider
The proposed Stanford Linear Collider (SLC) has been designed to provide 50 on 50 GeV electron-positron collisions. The performance of the 240 klystrons driving the two-mile long linac must be upgraded to achieve at least 50 Megawatts of peak power output at a pulse width of 5 µsec and a pulse repetition frequency of 180 pulses per second. The operating frequency of the upgraded linac will continue to be 2856 MHz. A klystron amplifier meeting these new requirements has been designed to operate at 315 KV, µk = 2, with a computed efficiency of slightly greater than 50%. Initial tests indicate the achievement of the basic power objectives; however, observed parasitic instabilities make beam focusing, RF drive frequency and drive level extremely critical. High electric fields in the electron gun, output gap and output window are all potential problems. Steps taken in the design to overcome these problems are discussed and test results are presented.
Second generation SLAC modulator
The Stanford Linear Accelerator Laboratory has undertaken the construction of a single pass electron-positron collider. In order to reach required beam energy 235 new klystrons needed upgraded modulator systems. The collider will use 50 GeV electrons and positrons. The increase in accelerator energy from the present 30 GeV necessitates the replacement of existing 35 MW klystrons with new 67 MW units. The doubling of klystron output power required a redesign of the modulator system. The 67 MW klystron needs a 350 kV beam voltage pulse with a 3.7 ..mu..s pulse width. A new pulse transformer was designed to deliver the increased voltage and pulse width. Pulse cable design was evaluated to obtain increased reliability of that critical element. The modulator, with the exception of its power supply, was rebuilt to produce the required power increase while enhancing reliability and improving maintainability. An investigation of present thyratron switch tube performance under the new operating conditions resulted in agitation and some warranted panic but these conditions were mitigated after several successful experiments and some evolutionary narrowing of the klystron pulse width. The discussion will cover the upgraded modulator system specifications and some details of the new pulse transformer tank, pulse cable, modulator,more » and modulator switch tube.« less
Bone changes in tuberous sclerosis mimicking metastases.
Sclerotic and lytic bone changes of tuberous sclerosis (TS) can mimic bone metastases. We report a case of bone metastases from bronchogenic carcinoma in a patient with TS bone changes. Bone scintigraphy and magnetic resonance imaging are useful in distinguishing the TS bone lesions from bone metastases.