Analysis of Dynamic Balance Test for Vertical Hydropower Unit
Targeted at broader vibration swing in a power plant unit capacity-enhancing transformation,analyzed the factors causing vibration,carried out dynamic balance test on the unit and balance treatment,achieved the ideal result.Through the test,summarized the dynamic balance test method on the vertical unit,offered a reference for other substation similar units.