Starting Short Circuit ＆ No－load Test of Bulb Type Hydrogenerator
：This paper discusses the method of treatment of hydrogenerator data in general short circuit and noload test．To fit in with general ruleall values have been expressed as per unit on rating and described in function．Here also adopted calculation of short circuit ratio、synchronous reactance、saturation coefficient．The reference mark of excitation current is the value of generator rotor＇s circuit when the stator current value was equal to the rated current in the course of three armature phases in short circuit．This way is different to the general ones．Such way does good to the calculating．