Poultry slaughterhouse wastewater treatment plant for high quality effluent.
This paper assesses a wastewater treatment plant (WWTP) regarding the technology used, as well as organic matter and nutrient removal efficiencies aiming to optimize the treatment processes involved and wastewater reclamation. The WWTP consists of a dissolved air flotation (DAF) system, an upflow anaerobic sludge blanket (UASB) reactor, an aerated facultative pond (AFP) and a chemical DAF system. The removal efficiencies of chemical oxygen demand (COD) (97.9 1.0% biochemical oxygen demand (BOD) (98.6 1.0% and oil and grease (O&G) (91.1 5.2% at the WWTP, the nitrogen concentration of 17 11 mg N NH3 and phosphorus concentration of 1.34 0.93 mg PO4( 3)/L in the final effluent indicate that the processes used are suitable to comply with discharge standards in water bodies. Nitrification and denitrification tests conducted using biomass collected at three AFP points indicated that nitrification and denitrification could take place in the pond.
Water science and technology a journal of the International Association on Water Pollution Research