further preferred features and advantages of the invention will appear from the following detailed examples and description given by way of example with reference to the accompanying drawings in which : fig1 shows a schematic cross - section of a first embodiment of an air treatment apparatus of the invention suitable for the removal of micro - organisms from air ; fig3 is a sectional elevation of a further embodiment illustrating a practical arrangement of the low power coronal discharge ozone generator therein ; fig4 is a front elevation of the embodiment of fig3 ; fig4 is a partly exploded perspective view the construction of the corona discharge device of the corona discharge ozone generator of the apparatus of fig1 ; fig5 shows a general perspective view of another embodiment of the invention ; and fig6 is an exploded perspective view illustrating the use of a single filter assembly for pre - and post - filtering . fig1 shows a schematic cross - section of an apparatus for the removal of micro - organisms from air according to the invention . 1 indicates the casing , 2 the inlet , 3 the fan , 4 an optional pre - filter , 5 the transformer , 6 the corona discharge ozone generator unit , 7 the outlet , and 8 the electrostatic post - filter . an inactivation zone 9 ( indicated schematically ) extends around the ozone generator unit 6 . fig2 and 3 show a practical arrangement of two ozone generator units 6 powered by a single common transformer unit 5 . in this case the direction of fan rotation is reversed with respect to that of the embodiment of fig1 so that the upper openings serve as the inlets 2 , and the openings adjacent the two fans 3 serve as the outlets 7 . fig4 is a partly exploded view showing the construction of the corona discharge ozone - generating unit 6 . 10 is the glass tube dielectric , 11 the outer mesh electrode , 12 the inner mesh electrode fitted with a spade end electrical connector 13 . when constructed the outer mesh 12 is rolled into a tube with a flange 14 providing a fixing means . 15 is an insulating plastic plate for mounting the assembly by means of insulating screws , nuts and washers 16 . fig5 shows a perspective view of one embodiment of the invention showing a casing 17 for a model with four outlet apertures 7 for respective fans 3 . fig6 illustrates the use of a single common filter assembly 18 in a two - fan device 19 to provide both pre - and post - filtering . this configuration is especially useful for removal of smoke . the unit comprises a force chamber partially contained by casing 20 , fitted with a filter holder 21 provided with lugs 22 for snap - fit interengagement with mounting points 23 on the front face 24 of the casing 20 . the inlets 2 and outlets 7 are disposed in upper and lower portions 25 , 26 , respectively , of the front face 24 . the filter holder 21 supports the filter assembly 18 across both the upper and lower portions 25 , 26 of the front face 24 . in this example there is provided an external filter 27 which is a 3m low pressure 3202wat filtrete ™ tobacco smoke filter . inside this is a second filter 28 , in this case a 3m filtrete ™ haf filter . the force chamber 20 contains two fans 3 , which draw air 29 into the unit 20 . as a result , the smoke laden air is first drawn through the upper area 30 of the two filter layers 27 , 28 into the unit 20 , passes through the low power corona discharge field ( not shown ) and then exits through a lower area 31 of the two filter layers 27 , 28 . with reference to fig1 , the apparatus comprises a containment means consisting of a casing ( 1 ), in this case of thin sheet metal construction . this casing has an inlet ( 2 ) fitted with an electrically - driven fan ( 3 ) so positioned as to produce an efficient flow of air into the apparatus . the inlet may , optionally , have a pre - filter ( 4 ) fitted . within the casing is an approximately 4w corona discharge unit ( 6 ) operating at approximately 4 kv and lma . a transformer ( 5 ) supplies power to the corona discharge unit . in this case the outlet ( 7 ) is fitted with an electrostatic post - filter ( 8 , haf , filtrete ™ 3m corporation ) the details of the construction of the corona discharge unit are shown in fig4 . a silica glass tube dielectric ( 10 ) with a wall thickness of 0 . 8 - 1 . 1 mm has outer ( 11 ) and inner ( 12 ) essentially tubular stainless steel gauze electrodes . the dimensions are not critical but in this case the glass tube is approximately 63 mm long , inner electrode is formed from a 40 × 34 mesh number gauze of approximately 71 × 63 mm , and the outer electrode is formed from a coarser 24 × 28 mesh number gauze of approximately 133 × 63 mm . the inner electrode fits within the glass tube and is fitted with a spade end electrical connector ( 13 ). the outer electrode is formed into a cylinder fitting around the glass tube with a flange ( 14 ) allowing it to be fixed , together with the glass tube and inner electrode assembly , to a suitable insulating plastic base plate ( 15 ) by means of insulating nylon screws and washers and nuts ( 16 ). fig5 shows a casing suitable for use as a containment means , as described above . by configuring fans appropriately , air may by drawn in through the louvred apertures and out through the circular apertures , optionally through a post - filter . this arrangement is particularly suitable for use in an apparatus for the removal of micro - organisms from air . this unit has been tested for efficiency in microbiological tests for killing of airborne bacteria and fungal ( aspergillus niger ) spores and found to kill & gt ; 95 % at a flow rate of about 150 m 3 h − 1 . the output of ozone has also been tested and been found to be within the eh38 guidelines . the invention has been developed into a range of devices designed for microbiological decontamination of atmospheres . this embodiment employs closed - coupled field technology for the contained generation of an oxidising field , in tandem with electrostatic filtration of the air stream . combining these technologies in a manner that affords a high flow - rate permits the effective treatment of large volumes of atmosphere . this embodiment of the invention comprises four fans connected and switched so as to be progressively activated in order to provide a range of airflow rates : two modes of filtration were used in various experiments . either a hepa filter or an haf ( 3m filtrete ™) post - filter were fitted and their relative effects compared . the european standard for atmospheric levels of ozone is currently 0 . 2 ppm while , according to various literature sources the required dosage of ozone required to inactivate microbial systems , on contact , varies between 0 . 05 ppm and 0 . 4 ppm . an important aspect of this validation effort has been to demonstrate compliance of the device with european ozone emission standards , whilst additionally producing evidence of sufficient ozone generation to accommodate effective competence with regard to the task of broad scope anti - microbial activity . a key advantage of the device is the claim that ozone generation and reactions with micro - organisms , occur contained solely within the device resulting in decontamination with no measurable emission of ozone . ozone levels have been investigated employing a novel probe by which ozone production is determined by measurement of the degree of oxidation obtained with a d -□ tocopherol coating during exposure . trials have been conducted to measure ozone production within the device and the potential for environmental accumulation during use , with and without filter in situ . data indicate no significant emission of ozone from the device were detected over a 24 hour period in the operating environment . measurements indicate that significantly higher levels of ozone are produced within the closed coupled field device than predictably are required for contact inactivation all classes of micro - organisms for which susceptibility has been published . electrostatic air filtration is known to produce reduction in the levels air - borne microbial contaminants . a potential problem with stand - alone filtration devices is therefore the accumulation of possibly infective or otherwise unwanted viable contamination within the structure of the filter during life span . trials conducted to monitor these possibilities generated the following data showing the recovery of differing classes of organism from the interior surfaces of the terminal filter during different periods of operation in waste processing room . these data demonstrate that in an environment known to have high levels of air - borne microbial contamination no significant build up of viable organisms occurred in the filtration unit up to and including three months of use . this effect may caused by impingement of residual ozone on the active surfaces , loss of viability due to dehydration in the high flow rate of air , nutrient scarcity or a combination of these and other factors . such findings to some degree support the anti - microbial efficiency of the ozone generation system presented . more importantly these findings suggest that in respect of bacteria and fungi the filtration stage is unlikely to represent a biological hazard during replacement . the following experimental data reports on the performance of the device in relation to the reduction of single pass microbial challenges . performance at each of four flow rates has been determined for a range of organisms with and without electrostatic filtration in place . table 5 m4 / 4 single performance with no electrostatic filtration challenge speed 1 speed 2 speed 3 speed 4 level recovery recovery recovery recovery organism cfu / l − 1 cfu / l − 1 cfu / l − 1 cfu / l − 1 cfu / l − 1 a . niger 7 . 00e + 06 & lt ; 1 & lt ; 1 & lt ; 1 & lt ; 1 s . 8 . 40e + 06 & lt ; 1 & lt ; 1 & lt ; 1 & lt ; 1 typhimurium c . albicans 8 . 30e + 06 & lt ; 1 & lt ; 1 & lt ; 1 & lt ; 1 s . aureus 9 . 20e + 06 & lt ; 1 & lt ; 1 & lt ; 1 & lt ; 1 b . cereus 4 . 70e + 06 & lt ; 1 & lt ; 1 3 . 10e + 02 9 . 80e + 02 speed 1 = 160 m 3 / hour speed 2 = 320 m 3 / hour speed 3 = 480 m 3 / hour speed 4 = 540 m 3 / hour all conditions of treatment produced significant levels of reduction in the levels of air - borne challenges . under these challenge conditions speed 3 gave a 100 % performance with filter in place while speed 2 gave a 100 % performance with no filter in place . with filter in place all organisms were reduced to non - detectable levels at increment 4 with the exception of bacillus cereus , where only a 4 log reduction was achieved . it was noted that limiting the flow to speed 3 ( 480 m 3 / hour ) with the filter in situ , guaranteed a consistent and rapid degree of air processing . these experiments introduced a number of single calibrated doses of aspergillus niger hyphal fragments and spore particles into a chamber having an 8 1 − 1 volume . the chamber was constructed in a manner as to permit access of the quest device intake grill to the interior of the chamber while the output section vented directly into a second chamber of identical volume . both chambers were vented by membrane filters for the purpose of pressure equalisation . the purpose of the trial was to attempt to demonstrate a single pass efficiency in lethality in a known airborne pathogen . the biological material was delivered in the form of fungal hyphae and spores dispersed in calcium silicate matrix . both chambers were equipped with fans intended to assist dispersion . sampling was conducted via suction with collection in a 2 % sucrose / saline solution an involved 2 l − 1 volume for each chamber . the device was not operational during dosing for 2 minutes after the introduction of the biological material but had been previously stabilised for 30 minutes . after the post - dose period the device was operated for period of 1 minute and after which the atmosphere in the delivery chamber was sampled . recovery solutions were examined by serial dilution and survivors were estimated on oxytetracycline glucose yeast agar ( 5 days at 25 ° c .). the results of these counts provided estimates of the level of dosage and the level of survivors per 1 − 1 of atmosphere before and after treatment . tables 6 and 7 present the data obtained in this trial for instances of the device operating with either the electrostatic or hepa filter in place . in this series of trials a wide range of microbial types was continuously introduced at the intake section of the m4 / 4 device for a period of 1 hour . during the exposure time periodic measurements were taken at the output section and the levels of survivors determined . the following results were obtained . table 9 m4 / 4 performance : continuous input of viral particles mean cfu / m 3 / hr mean decline at input mean cfu / m 3 / hr log / cfu / m 3 / hr apparent treatment post treatment post treatment percentage organism class stream exit stream exit stream reduction ctx ss dna 4 . 3e + 12 8 . 1e + 02 & gt ; 12 & gt ; 99 . 999 scv - l - bc ds rna 9 . 2e + 12 4 . 6e + 02 & gt ; 12 & gt ; 99 . 999 fcov ss + rna 7 . 1e + 12 3 . 0e + 02 & gt ; 12 & gt ; 99 . 999 ( attenuated ) t4 phage ds dna 5 . 3e + 12 7 . 4e + 02 & gt ; 12 & gt ; 99 . 999 the device demonstrated a high level of competence in the inactivation of a wide range of micro - organisms including bacterial cells , bacterial spores , viral particles , mould , mould spores and yeasts . kill efficiencies in excess of log 12 were obtained consistently for all classes of viral particle examined , while for all other classes of organism no less than a log 5 kill was obtained on a continuous basis . in summary , the device is highly effective at killing micro - organisms . in spite of good compliance with glp standards laboratories may still develop problems associated with airborne microbial contamination . usually such problems are detected by routine environmental surveillance or incidences of contamination on solid agar plates . in this study a problem was investigated relating to a persistent environmental contamination in a commercial grain testing laboratory . this facility had reported significant levels of mould contamination of both blank plates and plates intended for the isolation of yeasts and moulds from samples . in - house environmental analysis by settle plate determined the presence of identical isolates to those found on the plates in the atmosphere of the incubation room . the isolate responsible for the contamination was confirmed as fusarium poae . this organism is common in temperate regions and is associated with commodities such as wheat and maize , both of which were commonly handled by the facility . it demonstrates growth over the range 2 . 5 °- 33 ° c . and , characteristically , produces profuse growth with salmon or pale pink colonies on common mycological media . the trial was conducted in two stages . during the first month of monitoring the m4 device was not in operation and air sampling was conducted on an hourly basis between the hours of 9 . 00 am and 5 6 . 00 pm over a six - day working week . sampling was conducted employing a cassela volumetric sampler with impaction onto oxytetracycline glucose yeast agar . during week one ( device off ) 0 . 1 , 0 . 2 , and 0 . 5 l − 1 air volumes were taken at the specified intervals . the device was operative during month two . sampling was conducted to the same schedule described above with an identical sampling procedure . simultaneously , during the trial records were kept of non - compliant contaminated agar intended for use in analytical procedures . results percentage in device f . poae lab plate status week cfu / l − 1 / air contamination off 1 17100 3 off 2 21300 2 off 3 16700 9 off 4 18900 3 mean 18500 4 . 25 on 5 20 & lt ; 1 on 6 40 & lt ; 1 on 7 2 & lt ; 1 on 8 3 & lt ; 1 mean 16 . 25 & lt ; 1 in this laboratory an overt problem had been experienced in relation to media contamination which was directly related to environmental cross - contamination with fusarium poae . the operation of the m4 / 4 device in the area that was the source of this problem successfully reduced the level of contamination on a consistent basis by between 2 and 3 log cycles l − 1 air . this magnitude of effect was sufficient to reduce the level of media contamination to a non - detectable level . on this basis , the m4 / 4 device has been shown to be an effective tool in the maintenance of a microbiological laboratory air quality . sanitisation of the atmosphere in a class ii microbiological laboratory waste room . a device according to the invention with a free fan transfer volume of 190 m 3 / hour fitted with either replaceable electrostatic ( flow rate = 160 m 3 / hour ) or hepa ( flow rate = 65 m 3 / hour ) post - filters was subjected to a practical evaluation in a class ii microbiological laboratory waste room . it was theorised that usage of electrostatic filtration in combination with a closed coupled field oxidation field would afford both reduction of airborne micro - organisms as well as good odour decontamination characteristics while employment of hepa filtration was anticipated to produce superior microbiological performance . assessment was by monitoring the reduction of airborne gram - negative bacteria over a seven day period in a microbiological laboratory waste - processing room . measurement included the performance characteristics of both filtration systems . the vast majority of contemporary microbiological laboratories are equipped with a designated area designed to afford physical segregation of contaminated biological waste intended for sanitation by autoclaving preceding safe disposal . such waste consists of agar plates , cultures and implements employed in microbiological manipulations . in general , such waste is extremely biologically active prior to treatment and may contain billions of organisms per gram . while every effort in glp is to prevent transfer of contaminants , the nature of the autoclaving process requires that storage bags are open to the atmosphere at the start of processing . as a consequence , the opportunity exists for the introduction of large masses of organisms or spores into the environment . factually , such areas exhibit high levels of airborne contamination . these distribution factors coupled with the thermal currents created by autoclave operation engender a demonstrably abundant and sustained level of airborne micro - organisms of many differing types . it is true that such contamination is unlikely to present as a direct health risk through inhalation but such an environment provides a useful model for efficiency studies of devices , which purport to reduce airborne levels of micro - organisms . in this trial , the regime involved the sampling of the atmosphere in the test environment by impaction of air onto the surface of agar plates through the use of a cassela air - sampling device . the cassela unit is capable of accurately sampling a known volume of atmosphere over a 30 second period and continuously delivering the sampled air to an enclosed chamber . in this chamber an agar plate is exposed to column of intake air whilst rotating , thus distributing micro - organisms evenly over the surface of the plate . subsequent incubation of the plates allows enumeration of organisms present in the original volume of atmosphere examined . through the use of differing types of agar and diagnostic tests , it is possible to differentially count different types or classes of micro - organism . the room comprised a 24 . 3 m 3 cube . it contained an autoclave with treated waste in one half and 25 kg storage bags of untreated waste in the remaining floor area . at any one time the area contained a minimum of 16 untreated waste bags , of which between 8 and 10 bags were be handled and processed in a working day between the hours of 9 . 00 am and 6 . 00 pm . the sampling device was located centrally . normally the room atmosphere was vented by forced extraction , but this was suspended during the trial . the autoclave hot exhaust was vented via an enclosed circuit , which was not thought to affect the atmospheric composition of the test environment . sampling occurred over a twenty - four hour period at the intervals given in table 11 below . such sampling extended over a seven - day period with the device running without any form of filtration in place and without the ozone generator switched on , to demonstrate the background level of contamination . the data obtained are given in tables 11 and 13 below . the data gathered in this exercise were employed as the comparison set for all information gathered during the subsequent period when the device was operational as a sanitising unit . two further identically - scheduled sampling periods were conducted sequentially separated by a four day recovery gap . firstly , the device was operated with the corona discharge unit on and an electrostatic filter in place . in the second session the device was operated with a hepa filter in place , again with an identical sampling plan . the agar employed in all tests was violet red bile glucose agar ( vrbga ) intended for the recovery of gram - positive organisms from the atmosphere through the use of the cassela device . colonies were recovered on this agar after incubation at 35 ° c . for 24 hours . as the trials were intended primarily to show overall comparisons , it was assumed that all isolates obtained on vrbga were gram - negative and all isolates were counted . colonies were further differentiated on the basis of oxidase reaction . all sampling was conducted in duplicate . table 11 below presents the data obtained for gram - negative ( ox + ve and ox − ve ) isolates during the unsanitised control period and that for the data obtained during the period of oxidation treatment associated with electrostatic filtration of the return air flow . table 12 illustrates the average percentage kill through out the day attributable to the action of oxidation treatment and electrostatic filtration . tables 13 and 14 summarise the same categories of data obtained for the period when sanitisation was attempted employing oxidation and hepa filtration . table 14 mean microbial % reduction levels over a 24 - hour period in a microbiological waste room ( 23 . 4 m 3 ) with device operating with hepa filtration . 06 : 00 o 3 on hepa + 34 . 5 33 . 9 10 : 00 o 3 on hepa + 30 . 3 33 . 1 14 : 00 o 3 on hepa + 28 . 6 28 . 7 18 : 00 o 3 on hepa + 22 . 1 24 . 6 20 : 00 o 3 on hepa + 19 . 2 17 . 4 02 : 00 o 3 on hepa + 29 . 6 28 . 2 04 : 00 o 3 on hepa + 34 . 8 34 . 2 the data given in tables 11 - 14 indicate that the test environment under conditions of no treatment did exhibit 10 elevated levels of airborne microbial contamination . in the same tables it is observed that irrespective of the filter type employed with device , measurable reduction of airborne levels of gram negative bacteria was achieved . on a continuous use basis with active replacement of micro - organisms into the environment , operation with electrostatic filtration gave an average of 84 % reduction of gram negative bacteria ( ox + ve and − ve ). this amounts to a continuous overall reduction of between 1 and 2 log cycles . by comparison the unit gave only 28 % reduction when operated with hepa . filtration . in theory , hepa filtration should provide greater efficiency with respect to microbial removal but under the trial conditions we calculated that with this form of filtration in place the device was capable of only 2 . 7 room changes per hour . it is apparent this was an insufficient flow rate to achieve high levels of reduction in an environment to which micro - organisms are constantly being added . in the case of operation with electrostatic filtration 7 . 1 room changes per hour were obtained , a factor which produced a much higher degree of impingement on the levels of airborne gram negative bacteria . both forms of filtration gave very high kill efficiencies during the single pass trials with aspergillus niger . in this case hepa in combination with ozonation gave 99 . 986 % reduction of challenge , which is close to the theoretical performance . on the other hand electrostatic filtration in combination with ozonation gave 98 . 012 % reduction of challenge . overall , the data favour the combination of closed coupled filed oxidation with electrostatic filtration . this configuration affords high flow rates with very high levels of kill in an environment where recontamination of sanitised air is continuous . by comparison with other commercial units the kill rate in the waste room environment may be considered very significant . the principle of drawing air through a field of high oxidation potential sufficient to oxidise many organic pollutants is equally applicable to the removal of unpleasant or unwanted odours , where these are caused by compounds capable of being oxidised to odourless products . the apparatus of the invention , optionally fitted with pre - and / or post - filters , preferably containing activated charcoal is highly suitable for this purpose . a sensory evaluation was conducted each day during operation of an m4 / 4 device in the microbiological waste processing facility . this involved subjective scoring by four people according to the key given with table 15 , below . evaluations were made for each type of filter and with the closed coupled oxidising field operating . the apparatus based in the casing shown in fig3 may be configured for the efficient removal of smoke from air . in this embodiment the fans may be so arranged as to draw air in through the circular apertures , preferably through a pre - filter , through the field of high ozone concentration and either out through the louvred apertures shown or back out through a post - filter arrangement . in one embodiment , particularly suitable for use in public areas such as public houses , hotels and bars is illustrated in fig4 . this apparatus ( the ‘ p6 ’ model ) is configured with two fans drawing air in through the filter assembly ( i . e . there is a pre - filter ) expelling air out through a different area of the filter assembly ( i . e . the air is also post - filtered ). the capacity of the apparatus is approximately 380 m 3 per hour . the filter assembly comprises an outer low pressure 3m 3202 wat tobacco smoke filter and an inner 3m filtrete ™ haf electrostatic filter . another , particularly preferred , embodiment is the ‘ p8 ’ device , which has four fans and is configured to draw air in through a filter assembly , preferably as described above , air being expelled through louvred apertures . the capacity of the apparatus is approximately 760 m 3 per hour . the core components of fan , closed coupled field unit and filters are common with the apparatus of example 1 . the efficiency of the device in reduction of eight types of tobacco - related toxic substances was tested in a test environment . these substances primarily occur in the atmosphere due to combustion of tobacco and the associated exhalation of smoke from combusted tobacco . a list of the analytes determined is given in table 17 below . the test environment consisted of a public house pool room with a volume of 84 m 3 into which the p8 unit was installed . during the operation the device , per specification , was predicted to change and process the environment within this room at a rate 9 times per hour . common practice prior to the trial was to evacuate the atmosphere by forced and passive ventilation . these systems of air purification were considered unsatisfactory by the proprietor of the property , especially during the winter , due to the requirement to compensate for massive heat loss . after installation of the p8 device , air sampling was conducted in the pool room for seven days , between the hours of 8 . 00 pm and 9 . 00 pm at a rate of 5 m 3 per hour , without the device in operation . this provided background control data for all analytes . a further set of control data was obtained at 5 . 0 pm which represents a point after normal ventilation when the room is not used for pool or smoking . the data relating to this point may be considered base level for all analytes . during the subsequent seven days the sampling procedure was repeated with the device in operation , with the goal of determining the efficiency of atmospheric clean up . during the trial an estimate was made of the daily cigarette consumption during the sampling interval . sampling was conducted by the use of a vacuum device with collection of sampled atmosphere in either phosphate buffer or an acetonitrile : methanol phase . analytes were determined quantitatively employing the following analytical techniques : gas / liquid chromatography , hplc diode array and differential pulse polarography . table 16 below describes the pattern of cigarette consumption recorded for the test environment during the sampling periods . table 17 describes the mean levels of analytes recorded during the control period and during the period of sampling when the p8 device was activated . this table also describes the contribution to air quality attributable to the device in terms of percentage reduction of airborne toxic substances . table 17 mean level of tobacco smoke analytes in the atmosphere in a public house pool room for a seven day period with and without the p8 unit in operation mean mean mean level 5pm level 9pm level 9pm mean no treatment no treatment with treatment reduction analyte unit device off device off device on due to treatment carbon monoxide mg / m 3 0 . 82 7 . 1 0 . 4 94 . 4 3 - ethenylpyridine mg / m 3 0 . 17 37 . 6 0 . 4 98 . 9 formaldehyde mg / m 3 0 . 33 84 . 2 0 . 2 99 . 8 acetaldehyde mg / m 3 0 . 01 196 . 3 0 . 4 99 . 8 ammonia mg / m 3 0 . 01 103 . 5 0 . 8 99 . 2 nicotine mg / m 3 0 . 96 61 . 4 1 . 06 98 . 3 total phenolics mg / m 3 0 . 11 12 . 7 0 . 2 98 . 4 total cresols mg / m 3 0 . 06 3 . 8 0 . 08 98 . 9 the test data demonstrates that operation of the p8 device produced highly significant reduction in all levels of tobacco smoke analytes with overall analyte clearance rates over the range 97 . 9 to 99 . 8 %. the level of reduction is such that the residue levels during device operation are not significantly different from background level during periods when the room was in disuse . considering the findings and that there was virtually constant replacement of the analytes to the atmosphere , p8 device performed in a highly efficient manner in the removal of toxic tobacco smoke contaminants . a particularly useful application of the invention is its incorporation into air - conditioning ducting in buildings and , in particular , in aircraft . a preferred embodiment comprises a cartridge assembly , through which air flows , comprising one or more corona discharge unit as herein described , optionally with one or more filter assemblies . in this situation , the pressure within the duct may be sufficient to allow a suitable flow of air through the cartridge assembly without the further use of fans or impellers . it has been found that one 5w corona discharge unit , as described , per approximately 500 m 3 per hour throughput of air is suitable . such units are useful in clearing air of micro - organisms , odours , and smoke . the leakage of ozone from an operating am4 unit ( 190 m 3 h − 1 airflow , one 5w corona discharge unit ) was measured when the air filtration system was operated in 4 different modes : ( i ) filter in and corona discharge unit on ; ( ii ) filter out and corona discharge unit on ; ( iii ) filters in and corona discharge unit off , and ( iv ) filters out and corona discharge unit off . the ozone levels were measured at 0 , 0 . 5 and 1 . 0 m from the emitting face of the unit . the distance was measured using a metre rule and was checked at intervals during the experiment by the operator . the experiment was performed on 19 jun . 2002 in a laboratory that was at a temperature of 22 ° c . the ozone measurement was performed using gastec detection tubes ( no . 18l ). the 18l range provides a rapid , fully quantitative analysis of the concentration of ozone in air with an accuracy of ± 25 %. the manufacturer states that the minimum detectable concentration as 0 . 01 ppm . the gastec tubes were purchased specifically for this work and were marked valid until may 2005 . a gastec multi - stroke gas sampling pump was used in conjunction with the tubes . the principle of the gas tube operation is described by equation 1 below . 2o 3 + c 16 h 10 n 2 o 2 → 2c 8 h 5 no 2 + 2o 2 eqn ( 1 ). the ozone in air , once sucked up through the tube , bleaches the indigo ( c 16 h 10 n 2 o 2 , blue ) to form isatin ( c 8 h 5 no 2 ), which is white in colour . for each position , i . e . 0 , 0 . 5 and 1 . 0 m from the emitting surface , ( at an approximate angle of 90 °) and each operational mode , a tube was placed in the pump and held in position manually . the system was left to stabilize for 5 minutes and then 10 pumps ( equivalent to 1000 cm 3 volume ) were drawn on the hand pump . each pump lasted an average of 30 seconds . the measurement for each combination of position and operational mode was repeated five times . the individual results for each tube are shown in table 18 . the readings were very small such that the highest readings only coloured the first graduation on the gastec tube . the highest reading was recorded when the tube was placed at the emitting surface and the filter was in and the korona was on . the next highest reading was recorded with the korona on , but the filter out . all other positions and operational combinations produced no change of colour on the gastec tube indicating the levels of ozone , if present , were less than 0 . 01 ppm . the average gap in the gastec tube through which the air is drawn was 1 mm . the analysis system used is known as active sampling . five replicate tubes were used for each combination to help account for the potential variability in the positioning of the gastec tube within the flow of air exiting from the air filtration system . the tests are were designed to determine whether a significant concentration of ozone accumulated in a confined space in which an am4 unit operated over an 8 hour period as measured by passive sampling . the test was performed in a room of approximately 36 . 75 m 3 ( 3 . 5m × 3 . 5 m × 3 . 0 m ) receiving minimal natural light . ozone was measure by a number of sampling cards ( afc international inc , usa ). 1 . chromair ozone cards 2 . chromair nitrogen cards 3 . safeair ozone cards 4 . safeair nitrogen dioxide cards nitrogen dioxide is a potential positive interferent beyond 0 . 3 ppm with both ozone sampling cards and so its concentration was also monitored . average room temperature 19 ° c . sample cards were placed randomly on the floor , walls and suspended from the ceiling of the room . the cards were monitored for 8 hours with and without the unit operating . monitoring was every 15 minutes for the first hour and then after a further 7 hours . ‘ unit on ’-‘ unit off ’ values = 0 . 04 ppm time weighted average over 8 hour period hse occupational exposure limit ( oel ) for ozone over an 8 hour period is 0 . 2 ppm and the 15 minute exposure limit is set at 0 . 4 ppm . the recorded ozone leakage in the experiment was therefore well within ( 20 %) the 8 hour exposure limit .
the present invention provides an apparatus 1 for the treatment of air comprising a low power corona discharge ozone generator 5 , 6 inside a chamber 9 having an inlet 2 and an outlet 7 , and at least one air flow impeller 3 for inducing a flow of air through the chamber 9 . the ozone generator 5 , 6 is formed and arranged for generating a restricted concentration of ozone , within an inactivating zone 10 contained within the chamber 9 , through which the air flow is passed . the restricted concentration is sufficient to inactivate airborne pollutant material entrained in the air flow , yet decays sufficiently outside the inactivating zone so that the concentration of ozone in the cleaned air expelled from the apparatus 1 is at a physiologically acceptable level without the use of an ozone decomposition catalyzer .