It means Long time, Short time, Instantaneous, and ground fault.
The circuit breaker must detect a fault condition; in low voltage circuit breakers this is usually done within the breaker enclosure. Circuit breakers for large currents or high voltages are usually arranged with protective relay pilot devices to sense a fault condition and to operate the trip opening mechanism. A circuit breaker is an automatically operated electrical switch designed to protect an electrical circuit from damage caused by overload or short circuit. The World's most comprehensive professionally edited abbreviations and acronyms database. All trademarks/service marks referenced on this site are properties of their respective owners. The Acronym Finder is ©1988-2015, Acronym Finder, All Rights Reserved.  LSIG = A combination of adjustable trip functions including long-time ampere rating, long-time delay, short-time pickup, short-time delay, defeatable instantaneous pickup, ground-fault pickup and ground-fault delay. ------------------------- Regards, Brian. Top: Bottom. LIG = A combination of adjustable trip functions including long-time ampere rating, long-time delay, Circuit breakers with LI, LSI or LSIG trip functions would not require the documentation and one of the means specified in 240.87, even if the “I” setting switch has an OFF position.This section does not apply to thermal-magnetic circuit breakers as they all have an instantaneous trip function. All Square D molded case, insulated case and low voltage power circuit breakers are equipped with an instantaneous trip function and thus do not require documentation, ZSI, differential relaying or energy-reducing maintenance switching. This means that as current increases, the time that it takes the device to trip will decrease. In order to coordinate better with these types of downstream devices, Micrologic circuit breakers offer inverse time delay characteristics on the long-time, short-time and ground-fault functions. This means that the equipment has undergone additional testing to verify that it can handle. Electronic Trip Circuit Breaker Basics 0600DB1104Section 1—Electronic Trip Circuit Breakers 03/20126 © 2012 Schneider Electric All Rights Reserved the additional heat rise associated with this level of operation. Best Answer: LSIG is common among all manuf with the definitions above. LSIA is a term used primarily by Westinghouse/Culter Hammer. The LSI are the same as above. The A means that the ground fault function is an Alarm only and will not trip the brk. There is a Ground Fault LED that will light up if there is a ground fault on the system in excess of the setting. The breaker will not trip, just indicate an alarm. This style of ground fault is not used very much. Emergency systems, or processes where a non-orderly form of equipment shutdown is more dangerous than the ground fault itself. You can only have one or the other, LSIG or LSIA. LSG = A combination of adjustable trip functions including long-time ampere rating, long-time delay, short-time pickup, short-time delay, defeatable instantaneous pickup, ground-fault pickup and ground-fault delay. LIG = A combination of adjustable trip functions including long-time ampere rating, long-time delay, LSIG, Long time, Short time, Instantaneous, and ground fault are options that are available in breakers that electronic trip units. Breaker frames that have interchangeable trip units commonly start out with 250a frames, 400a, 600, 800, 1200a etc. Interrupting capacity has to do with the available fault current and nothing to do with LSIG. Getting a system coordination study can be of a benefit first to assure that the breakers are suitable for the available fault in different parts of the distribution system. I would just like to know more about LSIG breakers, firstly when (at what amperage) are they specified? What I have seen typically is that designers specify LSIG breakers once the service size/bus rating of the main swbd at and above 800A (@600V). However on smaller services (400A and below) - I dont usually see this being specified. We have sites with 30 amp and larger circuit breakers with LSIG. Interrupting capacity has to do with the available fault current and nothing to do with LSIG. Getting a system coordination study can be of a benefit first to assure that the breakers are suitable for the available fault in different parts of the distribution system. 630A, LSIG, LSIA are trip functions for the circuit breakers. L=long-time; S=short-time; I=instantaneous; G=ground fault; A=alarm. As for the meaning it is obvious from the definitions of the abbreviations! The breaker will not trip, just indicate an alarm. This style of ground fault is not used very much. Emergency systems, or processes where a non-orderly form of equipment shutdown is more dangerous than the ground fault itself. You can only have one or the other, LSIG or LSIA.
https://en.wikipedia.org/wiki/Circuit_breaker http://www.acronymfinder.com/LSIG.html http://www.theiet.org/forums/forum/messageview.cfm?catid=205&threadid=34057 http://static.schneider-electric.us/docs/Circuit%20Protection/0100DB1019.pdf http://static.schneider-electric.us/docs/Circuit%20Protection/Low%20Voltage%20Power%20Circuit%20Breakers/0600DB1104.pdf https://sg.answers.yahoo.com/question/index?qid=20070916234327AAGS6qc http://www.theiet.org/forums/forum/messageview.cfm?catid=205&threadid=34057 http://forums.mikeholt.com/showthread.php?t=144204 http://forums.mikeholt.com/showthread.php?t=144204 https://sg.answers.yahoo.com/question/index?qid=20070916234327AAGS6qc
what does lsig mean
LSIG का क्या मतलब है
इसका अर्थ है लंबा समय, कम समय, तात्कालिक और जमीनी गलती।
सर्किट ब्रेकर को गलती की स्थिति का पता लगाना चाहिए; कम वोल्टेज सर्किट ब्रेकर में यह आमतौर पर ब्रेकर बाड़े के भीतर किया जाता है। बड़ी धाराओं या उच्च वोल्टेज के लिए सर्किट ब्रेकर आमतौर पर गलती की स्थिति को समझने और यात्रा खोलने के तंत्र को संचालित करने के लिए सुरक्षात्मक रिले पायलट उपकरणों के साथ व्यवस्थित होते हैं। एक सर्किट ब्रेकर एक स्वचालित रूप से संचालित विद्युत स्विच है जिसे विद्युत सर्किट को अधिभार या शॉर्ट सर्किट के कारण होने वाले नुकसान से बचाने के लिए डिज़ाइन किया गया है। दुनिया का सबसे व्यापक पेशेवर संपादित संक्षिप्ताक्षर और परिवर्णी शब्द डेटाबेस। इस साइट पर संदर्भित सभी ट्रेडमार्क/सेवा चिह्न उनके संबंधित स्वामियों की संपत्ति हैं। परिवर्णी शब्द खोजक 1988-2015, परिवर्णी शब्द खोजक, सर्वाधिकार सुरक्षित है ©।  LSIG = लंबे समय तक एम्पीयर रेटिंग, लंबे समय की देरी, कम समय पिकअप, कम समय की देरी, पराजेय तात्कालिक पिकअप, ग्राउंड-फॉल्ट पिकअप और ग्राउंड-फॉल्ट देरी सहित समायोज्य यात्रा कार्यों का एक संयोजन। ------------------------- सादर, ब्रायन। ऊपर: नीचे। LIG = लंबे समय तक एम्पीयर रेटिंग, लंबे समय की देरी सहित समायोज्य यात्रा कार्यों का एक संयोजन, LI, LSI या LSIG ट्रिप फ़ंक्शंस वाले सर्किट ब्रेकर को दस्तावेज़ीकरण और 240.87 में निर्दिष्ट साधनों में से एक की आवश्यकता नहीं होगी, भले ही "I" सेटिंग स्विच में OFF स्थिति हो। यह खंड थर्मल-चुंबकीय सर्किट ब्रेकर पर लागू नहीं होता है क्योंकि उन सभी में एक तात्कालिक यात्रा कार्य होता है। सभी स्क्वायर डी ढाला मामले, अछूता मामले और कम वोल्टेज पावर सर्किट ब्रेकर एक तात्कालिक यात्रा समारोह से लैस हैं और इस प्रकार प्रलेखन, जेडएसआई, अंतर रिलेइंग या ऊर्जा-कम करने वाले रखरखाव स्विचिंग की आवश्यकता नहीं है। इसका मतलब यह है कि जैसे-जैसे करंट बढ़ता है, डिवाइस को ट्रिप करने में लगने वाला समय कम होता जाएगा। आदेश में बहाव उपकरणों के इन प्रकार के साथ बेहतर समन्वय करने के लिए, Micrologic सर्किट तोड़ने लंबे समय के लिए व्युत्क्रम समय देरी विशेषताओं की पेशकश, कम समय और जमीन गलती कार्यों पर. इसका मतलब यह है कि उपकरण को यह सत्यापित करने के लिए अतिरिक्त परीक्षण से गुजरना पड़ा है कि यह संभाल सकता है। इलेक्ट्रॉनिक ट्रिप सर्किट ब्रेकर बेसिक्स 0600DB1104सेक्शन 1—इलेक्ट्रॉनिक ट्रिप सर्किट ब्रेकर 03/20126 © 2012 श्नाइडर इलेक्ट्रिक सर्वाधिकार सुरक्षित ऑपरेशन के इस स्तर से जुड़े अतिरिक्त गर्मी वृद्धि। सर्वश्रेष्ठ उत्तर: LSIG उपरोक्त परिभाषाओं के साथ सभी निर्माताओं में सामान्य है। एलएसआईए एक शब्द है जिसका उपयोग मुख्य रूप से वेस्टिंगहाउस/कल्टर हैमर द्वारा किया जाता है। एलएसआई ऊपर की तरह ही हैं। ए का मतलब है कि ग्राउंड फॉल्ट फ़ंक्शन केवल एक अलार्म है और बीआरके को ट्रिप नहीं करेगा। एक ग्राउंड फॉल्ट एलईडी है जो सेटिंग से अधिक सिस्टम पर ग्राउंड फॉल्ट होने पर प्रकाश करेगा। ब्रेकर ट्रिप नहीं करेगा, बस अलार्म का संकेत देगा। ग्राउंड फॉल्ट की इस शैली का बहुत अधिक उपयोग नहीं किया जाता है। आपातकालीन प्रणाली, या प्रक्रियाएं जहां उपकरण शटडाउन का एक गैर-व्यवस्थित रूप ग्राउंड फॉल्ट से अधिक खतरनाक है। आपके पास केवल एक या दूसरे, LSIG या LSIA हो सकते हैं। एलएसजी = लंबे समय तक एम्पीयर रेटिंग, लंबे समय की देरी, कम समय पिकअप, कम समय की देरी, पराजेय तात्कालिक पिकअप, ग्राउंड-फॉल्ट पिकअप और ग्राउंड-फॉल्ट देरी सहित समायोज्य यात्रा कार्यों का एक संयोजन। LIG = लंबे समय तक एम्पीयर रेटिंग, लंबे समय की देरी सहित समायोज्य यात्रा कार्यों का एक संयोजन, एलएसआईजी, लॉन्ग टाइम, शॉर्ट टाइम, इंस्टेंटियस, और ग्राउंड फॉल्ट ऐसे विकल्प हैं जो ब्रेकर में उपलब्ध हैं जो इलेक्ट्रॉनिक ट्रिप यूनिट हैं। ब्रेकर फ्रेम जिनमें विनिमेय ट्रिप इकाइयां होती हैं, आमतौर पर 250a फ्रेम, 400a, 600, 800, 1200a आदि से शुरू होती हैं। इंटरप्टिंग क्षमता का उपलब्ध फॉल्ट करंट से कोई लेना-देना नहीं है और एलएसआईजी से कोई लेना-देना नहीं है। सिस्टम समन्वय अध्ययन प्राप्त करना पहले यह सुनिश्चित करने के लिए एक लाभ हो सकता है कि ब्रेकर वितरण प्रणाली के विभिन्न हिस्सों में उपलब्ध गलती के लिए उपयुक्त हैं। मैं सिर्फ एलएसआईजी ब्रेकर के बारे में अधिक जानना चाहता हूं, सबसे पहले जब (किस एम्परेज पर) वे निर्दिष्ट हैं? मैंने आम तौर पर जो देखा है वह यह है कि डिजाइनर 800 ए (@600V) पर और उससे ऊपर मुख्य एसडब्ल्यूबीडी की सेवा आकार/बस रेटिंग के बाद एलएसआईजी ब्रेकर निर्दिष्ट करते हैं। हालांकि छोटी सेवाओं (400 ए और नीचे) पर - मुझे आमतौर पर यह निर्दिष्ट नहीं दिख रहा है। हमारे पास एलएसआईजी के साथ 30 amp और बड़े सर्किट ब्रेकर वाली साइटें हैं। इंटरप्टिंग क्षमता का उपलब्ध फॉल्ट करंट से कोई लेना-देना नहीं है और एलएसआईजी से कोई लेना-देना नहीं है। सिस्टम समन्वय अध्ययन प्राप्त करना पहले यह सुनिश्चित करने के लिए एक लाभ हो सकता है कि ब्रेकर वितरण प्रणाली के विभिन्न हिस्सों में उपलब्ध गलती के लिए उपयुक्त हैं। 630A, LSIG, LSIA सर्किट ब्रेकर के लिए ट्रिप फंक्शन हैं। एल = लंबे समय तक; एस = अल्पकालिक; मैं=तात्कालिक; जी = जमीन गलती; ए = अलार्म। अर्थ के लिए, यह संक्षिप्ताक्षरों की परिभाषाओं से स्पष्ट है! ब्रेकर ट्रिप नहीं करेगा, बस अलार्म का संकेत देगा। ग्राउंड फॉल्ट की इस शैली का बहुत अधिक उपयोग नहीं किया जाता है। आपातकालीन प्रणाली, या प्रक्रियाएं जहां उपकरण शटडाउन का एक गैर-व्यवस्थित रूप ग्राउंड फॉल्ट से अधिक खतरनाक है। आपके पास केवल एक या दूसरे, LSIG या LSIA हो सकते हैं।