Loop Powered typically means that you have a singe, two-wire, in-line sensor, (transmitter, transducer), that derives it's operating power via the two wires, and modulates the loop current based on the process to be measured.
Instrumentation is the use of measuring instruments to monitor and control a process. It is the art and science of measurement and control of process variables within a production, laboratory, or manufacturing area.  RE: what is a &#39;loop&#39; test in instrumentation and control? After the installation of certain categories of instruments for example certain types of detectors, there is normally a test caried out to ascertain their integrity, one of these is the &#39;loop&#39; test.  Typical wiring for current output transducer. You can think of the current loop itself as being analogous to a water system. You have a hose pipe (the wires) and a source tap (the power supply). You have a spray gun that regulates the flow (the transducer). You can have other equipment on the line, but it all has to be connected together in a ring Ioop. A big benefit of the current loop is its simple wiring just the two wires. The supply voltage and measuring current are supplied over the same two wires. Zero offset of the base current (ie. 4mA) makes cable break detection simple: if the current suddenly drops to zero, you have a cable break. In electrical signalling an analog current loop is used where a device must be monitored or controlled remotely over a pair of conductors. Basic DC circuit theory shows that the current is the same all along the line. It was common to see 4–20 mA circuits that had loop lengths in miles or circuits working over telephone cable pairs that were longer than ten thousand feet end-to-end. There are still legacy systems in place using this technology. Depending on the source of current for the loop, devices may be classified as active (supplying power) or passive (relying on loop power). For example, a chart recorder may provide loop power to a pressure transmitter. Basic DC circuit theory shows that the current is the same all along the line. It was common to see 4–20 mA circuits that had loop lengths in miles or circuits working over telephone cable pairs that were longer than ten thousand feet end-to-end. There are still legacy systems in place using this technology. Discovering which power supply best meets your requirements is simple. In a current loop, the power supply must emit voltage equal to or greater than all the voltage drops in the system combined. The data acquisition device for this example uses a precision shunt resistor to measure current. You need to calculate the voltage drop across the resistor. For the example current loop system, your chosen transducer measures pressure and has an operating voltage of 12 to 30 V. With the transducer selected, properly measuring the current signal is required to provide an accurate representation of the pressure applied to the transducer. (For example, a thermocouple isa type of sensor which provides a very low-level output voltage that isproportional to its ambient temperature.) The transmitter amplifiesand conditions the sensor’s output, and then converts this voltage toa proportional 4-20mA dc-current that circulates within the closedseries-loop. For example, when a loop-poweredapplication is powered from a 24V power source, the sum of all thevoltage drops around the series loop has to also equal 24V. Everycomponent through which the 4-20mA loop current passes developsa maximum voltage drop equal to that component’s resistancemultiplied by 0.020 Amperes (20mA). A current loop can also be used to control a valve positioner or other output actuator. An analog current loop can be converted to a voltage input with a precision resistor. Basic DC circuit theory shows that the current is the same all along the line. It was common to see 4–20 mA circuits that had loop lengths in miles or circuits working over telephone cable pairs that were longer than ten thousand feet end-to-end. There are still legacy systems in place using this technology. Loop Powered typically means that you have a singe, two-wire, in-line sensor, (transmitter, transducer), that derives it's operating power via the two wires, and modulates the loop current based on the process to be measured. Depends on your definition of branch-off. You can have a power supply that is capable of supplying multiple loops, however, EACH sensor is supplied by ONE loop. You cannot power more than one sensor off a loop.... As JRaef put it, each loop supply is limited as to what it will supply. The loop-powered sensor is in a remote location and gets its operating power from the source end over the single pair of wires. The sensor also controls the current in the single loop to give process information back to the source measuring equipment. An alternate to this device would be a 4-wire device, where constant power is applied to 2-wires to supply the sensor, and the snesor modulates a signal on a second pair of wires. Depends on your definition of branch-off. You can have a power supply that is capable of supplying multiple loops, however, EACH sensor is supplied by ONE loop. You cannot power more than one sensor off a loop.... As JRaef put it, each loop supply is limited as to what it will supply.
https://en.wikipedia.org/wiki/Instrumentation https://answers.yahoo.com/question/index?qid=20070918061030AASHm5B http://www.sensorland.com/HowPage028.html https://en.wikipedia.org/wiki/Current_loop https://en.wikipedia.org/wiki/Current_loop http://www.ni.com/white-paper/6940/en/ http://www.pacontrol.com/download/4-20mA-Current-Loop-Primer.pdf https://en.wikipedia.org/wiki/Current_loop http://www.electriciantalk.com/f2/loop-powered-34499/ http://www.electriciantalk.com/f2/loop-powered-34499/
what is loop power instrumentation
लूप पावर इंस्ट्रूमेंटेशन क्या है
लूप संचालित आम तौर पर इसका मतलब है कि आपके पास एक सिंग, टू-वायर, इन-लाइन सेंसर, (ट्रांसमीटर, ट्रांसड्यूसर) है, जो दो तारों के माध्यम से इसकी ऑपरेटिंग पावर प्राप्त करता है, और मापा जाने वाली प्रक्रिया के आधार पर लूप करंट को नियंत्रित करता है।
इंस्ट्रूमेंटेशन एक प्रक्रिया की निगरानी और नियंत्रण के लिए मापने वाले उपकरणों का उपयोग है। यह उत्पादन, प्रयोगशाला या विनिर्माण क्षेत्र के भीतर प्रक्रिया चर के माप और नियंत्रण की कला और विज्ञान है।  आरई: इंस्ट्रूमेंटेशन और नियंत्रण में एक &#39;लूप&#39; परीक्षण क्या है? कुछ श्रेणियों के उपकरणों की स्थापना के बाद, उदाहरण के लिए कुछ प्रकार के डिटेक्टर, आम तौर पर उनकी अखंडता का पता लगाने के लिए एक परीक्षण किया जाता है, इनमें से एक &#39;लूप&#39; परीक्षण है।  वर्तमान आउटपुट ट्रांसड्यूसर के लिए विशिष्ट वायरिंग। आप वर्तमान लूप को जल प्रणाली के अनुरूप होने के बारे में सोच सकते हैं। आपके पास एक नली पाइप (तार) और एक स्रोत नल (बिजली की आपूर्ति) है। आपके पास एक स्प्रे बंदूक है जो प्रवाह (ट्रांसड्यूसर) को नियंत्रित करती है। आपके पास लाइन पर अन्य उपकरण हो सकते हैं, लेकिन यह सब एक रिंग Ioop में एक साथ जुड़ा होना चाहिए। वर्तमान लूप का एक बड़ा लाभ इसकी सरल वायरिंग है, केवल दो तार। आपूर्ति वोल्टेज और मापने वाले वर्तमान को एक ही दो तारों पर आपूर्ति की जाती है। बेस करंट का शून्य ऑफसेट (यानी 4mA) केबल ब्रेक का पता लगाना सरल बनाता है: यदि करंट अचानक शून्य हो जाता है, तो आपके पास केबल ब्रेक होता है। विद्युत सिग्नलिंग में, एक एनालॉग करंट लूप का उपयोग किया जाता है जहां एक उपकरण को कंडक्टरों की एक जोड़ी पर दूर से मॉनिटर या नियंत्रित किया जाना चाहिए। बुनियादी डीसी सर्किट सिद्धांत से पता चलता है कि वर्तमान सभी लाइन के साथ समान है। 4-20 एमए सर्किट को देखना आम था, जिसमें मील या सर्किट में लूप की लंबाई टेलीफोन केबल जोड़े पर काम कर रही थी जो दस हजार फीट से अधिक लंबे थे। इस तकनीक का उपयोग करके अभी भी विरासत प्रणालियां हैं। लूप के लिए वर्तमान के स्रोत के आधार पर, उपकरणों को सक्रिय (बिजली की आपूर्ति) या निष्क्रिय (लूप पावर पर निर्भर) के रूप में वर्गीकृत किया जा सकता है। उदाहरण के लिए, एक चार्ट रिकॉर्डर एक दबाव ट्रांसमीटर को लूप पावर प्रदान कर सकता है। बुनियादी डीसी सर्किट सिद्धांत से पता चलता है कि वर्तमान सभी लाइन के साथ समान है। 4-20 एमए सर्किट को देखना आम था, जिसमें मील या सर्किट में लूप की लंबाई टेलीफोन केबल जोड़े पर काम कर रही थी जो दस हजार फीट से अधिक लंबे थे। इस तकनीक का उपयोग करके अभी भी विरासत प्रणालियां हैं। यह पता लगाना कि कौन सी बिजली आपूर्ति आपकी आवश्यकताओं को पूरा करती है, सरल है। करंट लूप में, बिजली की आपूर्ति को संयुक्त सिस्टम में सभी वोल्टेज बूंदों के बराबर या उससे अधिक वोल्टेज का उत्सर्जन करना चाहिए। इस उदाहरण के लिए डेटा अधिग्रहण डिवाइस वर्तमान को मापने के लिए एक सटीक शंट रोकनेवाला का उपयोग करता है। आपको रोकनेवाला के पार वोल्टेज ड्रॉप की गणना करने की आवश्यकता है। उदाहरण के लिए वर्तमान लूप सिस्टम, आपका चुना हुआ ट्रांसड्यूसर दबाव को मापता है और इसमें ऑपरेटिंग वोल्टेज 12 से 30 वी है। चयनित ट्रांसड्यूसर के साथ, ट्रांसड्यूसर पर लागू दबाव का सटीक प्रतिनिधित्व प्रदान करने के लिए वर्तमान सिग्नल को ठीक से मापना आवश्यक है। (उदाहरण के लिए, एक थर्मोकपल एक प्रकार का सेंसर है जो बहुत निम्न-स्तरीय आउटपुट वोल्टेज प्रदान करता है जो इसके परिवेश के तापमान के लिए आनुपातिक है। ट्रांसमीटर बढ़ाता है और सेंसर के आउटपुट की स्थिति रखता है, और फिर इस वोल्टेज को आनुपातिक 4-20mA डीसी-करंट में परिवर्तित करता है जो क्लोज्डसीरीज़-लूप के भीतर प्रसारित होता है। उदाहरण के लिए, जब एक लूप-संचालित अनुप्रयोग 24V पावर स्रोत से संचालित होता है, तो सभी का योगवॉल्यूमश्रृंखला लूप के चारों ओर वोल्टेज की बूंदें भी 24V के बराबर होती हैं। हर घटक जिसके माध्यम से 4-20mA लूप करंट गुजरता है, उस घटक के प्रतिरोध के बराबर अधिकतम वोल्टेज ड्रॉप विकसित होता है, जिसे 0.020 एम्पीयर (20mA) से गुणा किया जाता है। एक वर्तमान लूप का उपयोग वाल्व पोजिशनर या अन्य आउटपुट एक्ट्यूएटर को नियंत्रित करने के लिए भी किया जा सकता है। एक एनालॉग करंट लूप को एक सटीक रोकनेवाला के साथ वोल्टेज इनपुट में परिवर्तित किया जा सकता है। बुनियादी डीसी सर्किट सिद्धांत से पता चलता है कि वर्तमान सभी लाइन के साथ समान है। 4-20 एमए सर्किट को देखना आम था, जिसमें मील या सर्किट में लूप की लंबाई टेलीफोन केबल जोड़े पर काम कर रही थी जो दस हजार फीट से अधिक लंबे थे। इस तकनीक का उपयोग करके अभी भी विरासत प्रणालियां हैं। लूप संचालित आम तौर पर इसका मतलब है कि आपके पास एक सिंग, टू-वायर, इन-लाइन सेंसर, (ट्रांसमीटर, ट्रांसड्यूसर) है, जो दो तारों के माध्यम से इसकी ऑपरेटिंग पावर प्राप्त करता है, और मापा जाने वाली प्रक्रिया के आधार पर लूप करंट को नियंत्रित करता है। शाखा-बंद की आपकी परिभाषा पर निर्भर करता है। आपके पास एक बिजली की आपूर्ति हो सकती है जो कई छोरों की आपूर्ति करने में सक्षम है, हालांकि, प्रत्येक सेंसर को एक लूप द्वारा आपूर्ति की जाती है। आप एक लूप से एक से अधिक सेंसर को पावर नहीं दे सकते। जैसा कि जेआरएफ ने कहा है, प्रत्येक लूप आपूर्ति सीमित है कि यह क्या आपूर्ति करेगा। लूप-संचालित सेंसर एक दूरस्थ स्थान पर है और तारों की एकल जोड़ी पर स्रोत के अंत से अपनी ऑपरेटिंग शक्ति प्राप्त करता है। सेंसर स्रोत मापने वाले उपकरण को प्रक्रिया की जानकारी वापस देने के लिए एकल लूप में करंट को भी नियंत्रित करता है। इस डिवाइस का एक विकल्प एक 4-वायर डिवाइस होगा, जहां सेंसर की आपूर्ति के लिए 2-तारों पर निरंतर शक्ति लागू होती है, और स्नेसर तारों की दूसरी जोड़ी पर सिग्नल को नियंत्रित करता है। शाखा-बंद की आपकी परिभाषा पर निर्भर करता है। आपके पास एक बिजली की आपूर्ति हो सकती है जो कई छोरों की आपूर्ति करने में सक्षम है, हालांकि, प्रत्येक सेंसर को एक लूप द्वारा आपूर्ति की जाती है। आप एक लूप से एक से अधिक सेंसर को पावर नहीं दे सकते। जैसा कि जेआरएफ ने कहा है, प्रत्येक लूप आपूर्ति सीमित है कि यह क्या आपूर्ति करेगा।
लूप पॉवर इंस्ट्रुमेंटेशन म्हणजे काय?
इंस्ट्रुमेंटेशन म्हणजे एखाद्या प्रक्रियेचे निरीक्षण आणि नियंत्रण करण्यासाठी मोजमाप उपकरणांचा वापर. उत्पादन, प्रयोगशाळा किंवा उत्पादन क्षेत्रातील प्रक्रिया चरांचे मोजमाप आणि नियंत्रण करण्याची ही कला आणि विज्ञान आहे.  आरई: इंस्ट्रुमेंटेशन आणि कंट्रोलमध्ये &#39;लूप&#39; चाचणी म्हणजे काय? विशिष्ट प्रकारची उपकरणे उदाहरणार्थ विशिष्ट प्रकारचे डिटेक्टर बसवल्यानंतर त्यांची सत्यता पडताळून पाहण्यासाठी सामान्यत: चाचणी घेतली जाते, त्यापैकी एक म्हणजे &#39;लूप&#39; चाचणी.  सध्याच्या आउटपुट ट्रान्सड्यूसरसाठी विशिष्ट वायरिंग. आपण सध्याच्या लूपलाच पाण्याच्या प्रणालीशी साधर्म्य असल्याचे समजू शकता. आपल्याकडे एक नळ पाईप (वायर) आणि स्त्रोत नळ (वीज पुरवठा) आहे. आपल्याकडे एक स्प्रे गन आहे जी प्रवाह (ट्रान्सड्यूसर) नियंत्रित करते. आपल्याकडे लाइनवर इतर उपकरणे असू शकतात, परंतु हे सर्व रिंग आयओओपीमध्ये एकत्र जोडले जाणे आवश्यक आहे. सध्याच्या लूपचा एक मोठा फायदा म्हणजे त्याची साधी वायरिंग फक्त दोन वायर. पुरवठा व्होल्टेज आणि मापन प्रवाह याच दोन तारांवर पुरविला जातो. बेस करंटचा शून्य ऑफसेट (म्हणजे 4 एमए) केबल ब्रेक डिटेक्शन सोपा बनवतो: जर प्रवाह अचानक शून्यावर आला तर आपल्याकडे केबल ब्रेक आहे. इलेक्ट्रिकल सिग्नलिंगमध्ये एक अॅनालॉग करंट लूप वापरला जातो जिथे एखाद्या डिव्हाइसचे निरीक्षण किंवा संवाहकांच्या जोडीवर दूरस्थपणे नियंत्रित केले जाणे आवश्यक आहे. बेसिक डीसी सर्किट थिअरी दर्शविते की प्रवाह संपूर्ण रेषेवर समान आहे. मैलांमध्ये लूप लांबी असलेले 4-20 एमए सर्किट किंवा दहा हजार फुटांपेक्षा जास्त लांबीच्या टेलिफोन केबल जोड्यांवर काम करणारे सर्किट पाहणे सामान्य होते. या तंत्रज्ञानाचा वापर करून अजूनही वारसा व्यवस्था अस्तित्वात आहे. लूपसाठी प्रवाहाच्या स्त्रोतावर अवलंबून, डिव्हाइससक्रिय (वीज पुरवठा) किंवा निष्क्रिय (लूप पॉवरवर अवलंबून) म्हणून वर्गीकृत केले जाऊ शकतात. उदाहरणार्थ, चार्ट रेकॉर्डर प्रेशर ट्रान्समीटरला लूप पॉवर प्रदान करू शकतो. बेसिक डीसी सर्किट थिअरी दर्शविते की प्रवाह संपूर्ण रेषेवर समान आहे. मैलांमध्ये लूप लांबी असलेले 4-20 एमए सर्किट किंवा दहा हजार फुटांपेक्षा जास्त लांबीच्या टेलिफोन केबल जोड्यांवर काम करणारे सर्किट पाहणे सामान्य होते. या तंत्रज्ञानाचा वापर करून अजूनही वारसा व्यवस्था अस्तित्वात आहे. कोणता वीज पुरवठा आपल्या गरजा पूर्ण करतो हे शोधणे सोपे आहे. करंट लूपमध्ये, वीज पुरवठ्याने सिस्टममधील सर्व व्होल्टेज थेंबांच्या बरोबरीने किंवा त्यापेक्षा जास्त व्होल्टेज उत्सर्जित करणे आवश्यक आहे. या उदाहरणासाठी डेटा अधिग्रहण डिव्हाइस प्रवाह मोजण्यासाठी अचूक शंट प्रतिरोधक वापरते. आपल्याला रेसिस्टरमध्ये व्होल्टेज ड्रॉपची गणना करणे आवश्यक आहे. उदाहरणार्थ करंट लूप सिस्टीम, आपला निवडलेला ट्रान्सड्यूसर दाब मोजतो आणि त्याचा ऑपरेटिंग व्होल्टेज 12 ते 30 व्होल्टेज असतो. ट्रान्सड्यूसर ची निवड केल्याने, ट्रान्सड्यूसरला लागू केलेल्या दाबाचे अचूक प्रतिनिधित्व प्रदान करण्यासाठी सध्याच्या सिग्नलचे योग्य मोजमाप करणे आवश्यक आहे. (उदाहरणार्थ, थर्मोकपल एक प्रकारचा सेन्सर आहे जो त्याच्या सभोवतालच्या तापमानाच्या प्रमाणात अत्यंत कमी-स्तरीय आउटपुट व्होल्टेज प्रदान करतो.) ट्रान्समीटर सेन्सरचे आउटपुट वाढवते आणि अटी घालते आणि नंतर या व्होल्टेजचे रूपांतर क्लोजसीरिज-लूपमध्ये फिरणाऱ्या 4-20 एमए डीसी-करंटमध्ये करते. उदाहरणार्थ, जेव्हा लूप-संचालित अनुप्रयोग 24 व्ही पॉवर स्त्रोतापासून चालविला जातो, तेव्हा मालिकेच्या लूपभोवती च्या सर्व थेव्होल्टेज थेंबांची बेरीज देखील 24 व्ही इतकी असावी लागते. ज्या घटकातून ४-२० एमए लूप प्रवाह जातो, त्या घटकाच्या प्रतिकाराएवढा कमाल व्होल्टेज ड्रॉप ०.०२० अॅम्पीअर्स (२० एमए) ने गुणाकार होतो. व्हॉल्व्ह पोझिशनर किंवा इतर आउटपुट अॅक्च्युएटर नियंत्रित करण्यासाठी करंट लूप देखील वापरला जाऊ शकतो. एनालॉग करंट लूप अचूक प्रतिरोधकासह व्होल्टेज इनपुटमध्ये रूपांतरित केले जाऊ शकते. बेसिक डीसी सर्किट थिअरी दर्शविते की प्रवाह संपूर्ण रेषेवर समान आहे. मैलांमध्ये लूप लांबी असलेले 4-20 एमए सर्किट किंवा दहा हजार फुटांपेक्षा जास्त लांबीच्या टेलिफोन केबल जोड्यांवर काम करणारे सर्किट पाहणे सामान्य होते. या तंत्रज्ञानाचा वापर करून अजूनही वारसा व्यवस्था अस्तित्वात आहे. लूप पॉवर्ड चा अर्थ असा होतो की आपल्याकडे सिंग, टू-वायर, इन-लाइन सेन्सर, (ट्रान्समीटर, ट्रान्सड्यूसर) आहे, जो दोन तारांद्वारे ऑपरेटिंग पॉवर प्राप्त करतो आणि मोजण्याच्या प्रक्रियेच्या आधारे लूप करंट नियंत्रित करतो. आपल्या शाखा-ऑफच्या व्याख्येवर अवलंबून आहे. आपल्याकडे एक वीज पुरवठा असू शकतो जो एकाधिक लूपचा पुरवठा करण्यास सक्षम आहे, तथापि, प्रत्येक सेन्सर वन लूपद्वारे पुरविला जातो. आपण लूपमधून एकापेक्षा जास्त सेन्सरला पॉवर देऊ शकत नाही .... जेआरईएफने म्हटल्याप्रमाणे, प्रत्येक लूप पुरवठा तो काय पुरवठा करेल याबद्दल मर्यादित आहे. लूपवर चालणारा सेन्सर रिमोट लोकेशनमध्ये असतो आणि त्याची ऑपरेटिंग पॉवर सोर्स टोकापासून वायरच्या एका जोडीवर मिळते. स्त्रोत मापन उपकरणाला प्रक्रियेची माहिती परत देण्यासाठी सेन्सर सिंगल लूपमधील प्रवाहावर देखील नियंत्रण ठेवतो. या डिव्हाइसला पर्याय म्हणजे 4-वायर डिव्हाइस, जिथे सेन्सरचा पुरवठा करण्यासाठी 2-वायरवर सतत वीज लागू केली जाते आणि स्नेसर वायरच्या दुसर्या जोडीवर सिग्नल नियंत्रित करते. आपल्या शाखा-ऑफच्या व्याख्येवर अवलंबून आहे. आपल्याकडे एक वीज पुरवठा असू शकतो जो एकाधिक लूपचा पुरवठा करण्यास सक्षम आहे, तथापि, प्रत्येक सेन्सर वन लूपद्वारे पुरविला जातो. आपण लूपमधून एकापेक्षा जास्त सेन्सरला पॉवर देऊ शकत नाही .... जेआरईएफने म्हटल्याप्रमाणे, प्रत्येक लूप पुरवठा तो काय पुरवठा करेल याबद्दल मर्यादित आहे.
लूप पॉवर्ड चा अर्थ असा होतो की आपल्याकडे सिंग, टू-वायर, इन-लाइन सेन्सर, (ट्रान्समीटर, ट्रान्सड्यूसर) आहे, जो दोन तारांद्वारे ऑपरेटिंग पॉवर प्राप्त करतो आणि मोजण्याच्या प्रक्रियेच्या आधारे लूप करंट नियंत्रित करतो.