A wye connection is generally a four-wire system, comprising three line conductors and a neutral conductor, whereas a delta connection is a three-wire system, comprising three line conductors.
With a wye connection (also called a star connection) take our triangle above and use your wire cutters (literally) to cut the triangle apart at the corners. rearrange the three sides (transformer or motor windings) to form a Y. Where the three sides join in the center, connect a fourth wire. Call this wire neutral. The neutral is grounded at the service entrance. Wye systems must be used where you have single phase loads that you must feed. Interestingly, if you hide the neutral, you really can't tell the difference between star and delta systems. The phase-to-phase voltage is exactly the same. The main difference between star and delta is that in star, the phase voltage is root 3 multiplied by the line voltage making the speed of the machine to run at low speed whil … e in delta, the phase voltage is equal to the line voltage making the machine to run at high speed. The delta connection provides three line conductors, whereas the star connection provides three line conductors plus a neutral conductor. To obtain a single-phase supply, the load is connected either between any two line conductors, or between a line conductor and a neutral conductor. The transformer connection. Transformers can be connected in Wye (One side of each winding connected to the phase wire and the other connected to neutral or ground) or Delta (the polarity of each winding connected to the nonpolarity of another winding to form a triangle). The delta connection provides three line conductors, whereas the star connection provides three line conductors plus a neutral conductor. To obtain a single-phase supply, the load is connected either between any two line conductors, or between a line conductor and a neutral conductor. There is 120v from any phase to ground (neutral) with each winding at 120v, but 208v (120 x 1.73) between phases. The 480/277v Y system is connected the same way: 480v line-to-line and 277v line-to-ground. Now, back to our as-of-yet ungrounded Delta system for a moment. There are two ways of grounding a Delta system.  In wye-connected systems, the line voltage (line-to-line) is 1.732 times larger than the phase voltage (line-to-neutral). In a delta-connected system the line voltage is exactly the same as the phase voltage (line-to-line in both cases). The delta connection provides three line conductors, whereas the star connection provides three line conductors plus a neutral conductor. To obtain a single-phase supply, the load is connected either between any two line conductors, or between a line conductor and a neutral conductor. A significant difference between a delta and wye circuit is relative to the current flow. Looking at a typical wye connected load, the current flowing down a phase conductor flows through one leg or element of the load into the center conductor or neutral and back to the source. This holds for each of the three phases. Poly-phase circuits are often three-phase circuits in most industrial and commercial electrical distribution systems with wye and delta the most common. Loads in a wye circuits can be connected line-to-neutral as well as line-to-line, which can make the phase power flow calculations a bit confusing. In a wye system, the supply service line-to-line voltage is 1.73 times the voltage from any phase to neutral. Delta power is used for motors, 3-phase heaters, anywhere you don't need a neutral. The biggest use of delta is in power transmission. The neutral is grounded at the service entrance. Wye systems must be used where you have single phase loads that you must feed. Interestingly, if you hide the neutral, you really can't tell the difference between star and delta systems. The phase-to-phase voltage is exactly the same. A wye connection is generally a four-wire system, comprising three line conductors and a neutral conductor, whereas a delta connection is a three-wire system, comprising three line conductors. For a perfectly-balanced load (e.g. a three-phase motor), a wye-connected system can dispense with the neutral conductor. The delta connection provides three line conductors, whereas the star connection provides three line conductors plus a neutral conductor. To obtain a single-phase supply, the load is connected either between any two line conductors, or between a line conductor and a neutral conductor. The main difference between star and delta is that in star, the phase voltage is root 3 multiplied by the line voltage making the speed of the machine to run at low speed whil … e in delta, the phase voltage is equal to the line voltage making the machine to run at high speed. The neutral is grounded at the service entrance. Wye systems must be used where you have single phase loads that you must feed. Interestingly, if you hide the neutral, you really can't tell the difference between star and delta systems. The phase-to-phase voltage is exactly the same.
http://www.answers.com/Q/What_is_the_difference_between_an_electrical_3-phase_delta_connection_and_a_star_connection http://www.answers.com/Q/What_is_the_difference_between_Y_or_Wye_and_Delta_3_phase_power http://www.answers.com/Q/What_is_the_difference_between_Y_or_Wye_and_Delta_3_phase_power http://forums.mikeholt.com/showthread.php?t=84841 http://www.answers.com/Q/What_is_the_difference_between_Y_or_Wye_and_Delta_3_phase_power http://www.ecmag.com/section/your-business/wye-does-it-matter http://www.answers.com/Q/What_is_the_difference_between_an_electrical_3-phase_delta_connection_and_a_star_connection http://www.answers.com/Q/What_is_the_difference_between_Y_or_Wye_and_Delta_3_phase_power http://www.answers.com/Q/What_is_the_difference_between_an_electrical_3-phase_delta_connection_and_a_star_connection
what is the difference between delta and y electrical
डेल्टा और वाई इलेक्ट्रिकल में क्या अंतर है
एक वाई कनेक्शन आम तौर पर एक चार-तार प्रणाली होती है, जिसमें तीन लाइन कंडक्टर और एक तटस्थ कंडक्टर होता है, जबकि डेल्टा कनेक्शन एक तीन-तार प्रणाली होती है, जिसमें तीन लाइन कंडक्टर होते हैं।
वाई कनेक्शन (जिसे स्टार कनेक्शन भी कहा जाता है) के साथ हमारे त्रिकोण को ऊपर ले जाएं और त्रिकोण को कोनों पर अलग करने के लिए अपने वायर कटर (शाब्दिक) का उपयोग करें। वाई बनाने के लिए तीन पक्षों (ट्रांसफार्मर या मोटर वाइंडिंग) को पुनर्व्यवस्थित करें। जहां तीन पक्ष केंद्र में जुड़ते हैं, एक चौथा तार कनेक्ट करें। इस तार को न्यूट्रल कहते हैं। तटस्थ सेवा प्रवेश द्वार पर आधारित है। वाई सिस्टम का उपयोग किया जाना चाहिए जहां आपके पास एकल चरण भार है जिसे आपको खिलाना होगा। दिलचस्प बात यह है कि यदि आप तटस्थ छिपाते हैं, तो आप वास्तव में स्टार और डेल्टा सिस्टम के बीच अंतर नहीं बता सकते हैं। चरण-दर-चरण वोल्टेज बिल्कुल वैसा ही है। स्टार और डेल्टा के बीच मुख्य अंतर यह है कि स्टार में, चरण वोल्टेज रूट 3 को लाइन वोल्टेज से गुणा किया जाता है जिससे मशीन की गति कम गति से चलती है ... ई डेल्टा में, चरण वोल्टेज लाइन वोल्टेज के बराबर होता है जिससे मशीन उच्च गति पर चलती है। डेल्टा कनेक्शन तीन लाइन कंडक्टर प्रदान करता है, जबकि स्टार कनेक्शन तीन लाइन कंडक्टर और एक तटस्थ कंडक्टर प्रदान करता है। एकल-चरण आपूर्ति प्राप्त करने के लिए, लोड या तो किसी भी दो लाइन कंडक्टर के बीच, या एक लाइन कंडक्टर और एक तटस्थ कंडक्टर के बीच जुड़ा हुआ है। ट्रांसफार्मर कनेक्शन। ट्रांसफार्मर को वाई (प्रत्येक घुमावदार का एक पक्ष चरण तार से जुड़ा होता है और दूसरा तटस्थ या जमीन से जुड़ा होता है) या डेल्टा (प्रत्येक घुमावदार की ध्रुवीयता एक त्रिकोण बनाने के लिए दूसरे घुमावदार की गैर-ध्रुवीयता से जुड़ी होती है) में जोड़ा जा सकता है। डेल्टा कनेक्शन तीन लाइन कंडक्टर प्रदान करता है, जबकि स्टार कनेक्शन तीन लाइन कंडक्टर और एक तटस्थ कंडक्टर प्रदान करता है। एकल-चरण आपूर्ति प्राप्त करने के लिए, लोड या तो किसी भी दो लाइन कंडक्टर के बीच, या एक लाइन कंडक्टर और एक तटस्थ कंडक्टर के बीच जुड़ा हुआ है। 120v पर प्रत्येक घुमावदार के साथ किसी भी चरण से जमीन (तटस्थ) तक 120v है, लेकिन चरणों के बीच 208v (120 x 1.73)। 480/277v Y सिस्टम उसी तरह जुड़ा हुआ है: 480v लाइन-टू-लाइन और 277v लाइन-टू-ग्राउंड। अब, एक पल के लिए हमारे अभी तक भूमिगत डेल्टा सिस्टम पर वापस। डेल्टा प्रणाली को ग्राउंडिंग करने के दो तरीके हैं।  वाई-कनेक्टेड सिस्टम में, लाइन वोल्टेज (लाइन-टू-लाइन) फेज वोल्टेज (लाइन-टू-न्यूट्रल) से 1.732 गुना बड़ा होता है। डेल्टा से जुड़े सिस्टम में लाइन वोल्टेज बिल्कुल फेज वोल्टेज (दोनों मामलों में लाइन-टू-लाइन) के समान होता है। डेल्टा कनेक्शन तीन लाइन कंडक्टर प्रदान करता है, जबकि स्टार कनेक्शन तीन लाइन कंडक्टर और एक तटस्थ कंडक्टर प्रदान करता है। एकल-चरण आपूर्ति प्राप्त करने के लिए, लोड या तो किसी भी दो लाइन कंडक्टर के बीच, या एक लाइन कंडक्टर और एक तटस्थ कंडक्टर के बीच जुड़ा हुआ है। डेल्टा और वाई सर्किट के बीच एक महत्वपूर्ण अंतर वर्तमान प्रवाह के सापेक्ष है। एक विशिष्ट वाई कनेक्टेड लोड को देखते हुए, एक चरण कंडक्टर के नीचे बहने वाली धारा एक पैर या लोड के तत्व के माध्यम से केंद्र कंडक्टर या तटस्थ और स्रोत पर वापस बहती है। यह तीन चरणों में से प्रत्येक के लिए लागू होता है। पॉली-फेज सर्किट अक्सर अधिकांश औद्योगिक और वाणिज्यिक विद्युत वितरण प्रणालियों में तीन-चरण सर्किट होते हैं जिनमें वाई और डेल्टा सबसे आम होते हैं। वाई सर्किट में लोड को लाइन-टू-न्यूट्रल के साथ-साथ लाइन-टू-लाइन से जोड़ा जा सकता है, जो फेज पावर फ्लो की गणना को थोड़ा भ्रमित कर सकता है। वाई सिस्टम में, आपूर्ति सेवा लाइन-टू-लाइन वोल्टेज किसी भी चरण से तटस्थ तक वोल्टेज का 1.73 गुना है। डेल्टा पावर का उपयोग मोटर्स, 3-फेज हीटर के लिए किया जाता है, कहीं भी आपको न्यूट्रल की आवश्यकता नहीं होती है। डेल्टा का सबसे ज्यादा इस्तेमाल पावर ट्रांसमिशन में होता है। तटस्थ सेवा प्रवेश द्वार पर आधारित है। वाई सिस्टम का उपयोग किया जाना चाहिए जहां आपके पास एकल चरण भार है जिसे आपको खिलाना होगा। दिलचस्प बात यह है कि यदि आप तटस्थ छिपाते हैं, तो आप वास्तव में स्टार और डेल्टा सिस्टम के बीच अंतर नहीं बता सकते हैं। चरण-दर-चरण वोल्टेज बिल्कुल वैसा ही है। एक वाई कनेक्शन आम तौर पर एक चार-तार प्रणाली होती है, जिसमें तीन लाइन कंडक्टर और एक तटस्थ कंडक्टर होता है, जबकि डेल्टा कनेक्शन एक तीन-तार प्रणाली होती है, जिसमें तीन लाइन कंडक्टर होते हैं। पूरी तरह से संतुलित लोड (जैसे तीन-चरण मोटर) के लिए, एक वाई से जुड़ा सिस्टम तटस्थ कंडक्टर के साथ बांट सकता है। डेल्टा कनेक्शन तीन लाइन कंडक्टर प्रदान करता है, जबकि स्टार कनेक्शन तीन लाइन कंडक्टर और एक तटस्थ कंडक्टर प्रदान करता है। एकल-चरण आपूर्ति प्राप्त करने के लिए, लोड या तो किसी भी दो लाइन कंडक्टर के बीच, या एक लाइन कंडक्टर और एक तटस्थ कंडक्टर के बीच जुड़ा हुआ है। स्टार और डेल्टा के बीच मुख्य अंतर यह है कि स्टार में, चरण वोल्टेज रूट 3 को लाइन वोल्टेज से गुणा किया जाता है जिससे मशीन की गति कम गति से चलती है ... ई डेल्टा में, चरण वोल्टेज लाइन वोल्टेज के बराबर होता है जिससे मशीन उच्च गति पर चलती है। तटस्थ सेवा प्रवेश द्वार पर आधारित है। वाई सिस्टम का उपयोग किया जाना चाहिए जहां आपके पास एकल चरण भार है जिसे आपको खिलाना होगा। दिलचस्प बात यह है कि यदि आप तटस्थ छिपाते हैं, तो आप वास्तव में स्टार और डेल्टा सिस्टम के बीच अंतर नहीं बता सकते हैं। चरण-दर-चरण वोल्टेज बिल्कुल वैसा ही है।
डेल्टा आणि वाय इलेक्ट्रिकलमध्ये काय फरक आहे
वाई कनेक्शनसह (ज्याला स्टार कनेक्शन देखील म्हणतात) आमचा त्रिकोण वर घ्या आणि कोपऱ्यातील त्रिकोण तोडण्यासाठी आपले वायर कटर (अक्षरशः) वापरा. वाय तयार करण्यासाठी तीन बाजूंची (ट्रान्सफॉर्मर किंवा मोटर वळणे) पुनर्रचना करा. जिथे मध्यभागी तीन बाजू जोडतात, तेथे चौथी तार जोडावी. या वायरला न्यूट्रल म्हणा. तटस्थ सेवा प्रवेशद्वारावर ग्राऊंड केले जाते. आपल्याकडे सिंगल फेज लोड आहे तेथे वाई सिस्टम वापरणे आवश्यक आहे जे आपण फीड केले पाहिजे. विशेष म्हणजे, जर आपण तटस्थ लपवले तर आपण खरोखर स्टार आणि डेल्टा सिस्टममधील फरक सांगू शकत नाही. फेज-टू-फेज व्होल्टेज अगदी समान आहे. तारा आणि डेल्टा मधील मुख्य फरक असा आहे की ताऱ्यामध्ये, फेज व्होल्टेज रूट 3 लाइन व्होल्टेजने गुणाकार केला जातो ज्यामुळे मशीनचा वेग कमी वेगाने चालतो ... ई डेल्टामध्ये, फेज व्होल्टेज लाइन व्होल्टेजच्या बरोबरीने असते ज्यामुळे मशीन हाय वेगाने चालते. डेल्टा कनेक्शन तीन लाइन कंडक्टर प्रदान करते, तर स्टार कनेक्शन तीन लाइन कंडक्टर आणि एक तटस्थ कंडक्टर प्रदान करते. सिंगल-फेज पुरवठा मिळविण्यासाठी, भार एकतर कोणत्याही दोन लाइन कंडक्टरदरम्यान किंवा लाइन कंडक्टर आणि न्यूट्रल कंडक्टर दरम्यान जोडला जातो. ट्रान्सफॉर्मर कनेक्शन. ट्रान्सफॉर्मर वाय (प्रत्येक वळणाची एक बाजू फेज वायरशी जोडलेली आणि दुसरी तटस्थ किंवा जमिनीशी जोडलेली) किंवा डेल्टा (प्रत्येक वळणाची ध्रुवीयता दुसर्या वळणाच्या अध्रुवीयतेशी जोडून त्रिकोण तयार करणे) मध्ये जोडली जाऊ शकते. डेल्टा कनेक्शन तीन लाइन कंडक्टर प्रदान करते, तर स्टार कनेक्शन तीन लाइन कंडक्टर आणि एक तटस्थ कंडक्टर प्रदान करते. सिंगल-फेज पुरवठा मिळविण्यासाठी, भार एकतर कोणत्याही दोन लाइन कंडक्टरदरम्यान किंवा लाइन कंडक्टर आणि न्यूट्रल कंडक्टर दरम्यान जोडला जातो. कोणत्याही टप्प्यापासून जमिनीपर्यंत (न्यूट्रल) १२० व्ही असते आणि प्रत्येक वळण १२० व्होल्टवर असते, परंतु टप्प्यांदरम्यान २०८ व्ही (१२० बाय १.७३) असते. 480/277 व्ही वाय प्रणाली त्याच प्रकारे जोडली गेली आहे: 480 व्ही लाइन-टू-लाइन आणि 277 व्ही लाइन-टू-ग्राउंड. आता, क्षणभर ासाठी आपल्या अद्याप अस्तित्वात नसलेल्या डेल्टा प्रणालीकडे परत जा. डेल्टा प्रणाली ग्राऊंड करण्याचे दोन मार्ग आहेत.  वाई-कनेक्टेड सिस्टममध्ये, लाइन व्होल्टेज (लाइन-टू-लाइन) फेज व्होल्टेज (लाइन-टू-न्यूट्रल) पेक्षा 1.732 पट मोठा असतो. डेल्टा-कनेक्टेड सिस्टममध्ये लाइन व्होल्टेज फेज व्होल्टेज (दोन्ही प्रकरणांमध्ये लाइन-टू-लाइन) सारखेच असते. डेल्टा कनेक्शन तीन लाइन कंडक्टर प्रदान करते, तर स्टार कनेक्शन तीन लाइन कंडक्टर आणि एक तटस्थ कंडक्टर प्रदान करते. सिंगल-फेज पुरवठा मिळविण्यासाठी, भार एकतर कोणत्याही दोन लाइन कंडक्टरदरम्यान किंवा लाइन कंडक्टर आणि न्यूट्रल कंडक्टर दरम्यान जोडला जातो. डेल्टा आणि वाई सर्किटमधील एक महत्त्वपूर्ण फरक सध्याच्या प्रवाहाच्या सापेक्ष आहे. ठराविक वाई कनेक्टेड लोड पाहिल्यास फेज कंडक्टरच्या खाली वाहणारा प्रवाह भाराच्या एका पायातून किंवा घटकातून सेंटर कंडक्टर किंवा न्यूट्रलमध्ये जातो आणि परत स्त्रोताकडे जातो. हे तिन्ही टप्प्यांपैकी प्रत्येकासाठी आहे. पॉली-फेज सर्किट बहुतेक औद्योगिक आणि व्यावसायिक विद्युत वितरण प्रणालींमध्ये बहुतेकवेळा तीन-फेज सर्किट असतात ज्यात वाई आणि डेल्टा सर्वात सामान्य असतात. वाई सर्किटमधील लोड लाइन-टू-न्यूट्रल तसेच लाइन-टू-लाइन कनेक्ट केले जाऊ शकतात, ज्यामुळे फेज पॉवर फ्लो गणना थोडी गोंधळात टाकणारी होऊ शकते. वायई प्रणालीमध्ये, पुरवठा सेवा लाइन-टू-लाइन व्होल्टेज कोणत्याही टप्प्यापासून न्यूट्रलपर्यंत व्होल्टेजच्या 1.73 पट असतो. डेल्टा पॉवरचा वापर मोटर्स, 3-फेज हीटरसाठी केला जातो, जिथे आपल्याला न्यूट्रलची आवश्यकता नसते. डेल्टाचा सर्वाधिक वापर पॉवर ट्रान्समिशनमध्ये होतो. तटस्थ सेवा प्रवेशद्वारावर ग्राऊंड केले जाते. आपल्याकडे सिंगल फेज लोड आहे तेथे वाई सिस्टम वापरणे आवश्यक आहे जे आपण फीड केले पाहिजे. विशेष म्हणजे, जर आपण तटस्थ लपवले तर आपण खरोखर स्टार आणि डेल्टा सिस्टममधील फरक सांगू शकत नाही. फेज-टू-फेज व्होल्टेज अगदी समान आहे. वाई कनेक्शन ही सामान्यत: चार-वायर प्रणाली असते, ज्यात तीन लाइन कंडक्टर आणि एक तटस्थ कंडक्टर असतात, तर डेल्टा कनेक्शन ही तीन-वायर प्रणाली असते, ज्यात तीन लाइन कंडक्टर असतात. पूर्णपणे संतुलित लोडसाठी (उदा. थ्री-फेज मोटर), वाई-कनेक्टेड सिस्टम न्यूट्रल कंडक्टरसह वितरीत करू शकते. डेल्टा कनेक्शन तीन लाइन कंडक्टर प्रदान करते, तर स्टार कनेक्शन तीन लाइन कंडक्टर आणि एक तटस्थ कंडक्टर प्रदान करते. सिंगल-फेज पुरवठा मिळविण्यासाठी, भार एकतर कोणत्याही दोन लाइन कंडक्टरदरम्यान किंवा लाइन कंडक्टर आणि न्यूट्रल कंडक्टर दरम्यान जोडला जातो. तारा आणि डेल्टा मधील मुख्य फरक असा आहे की ताऱ्यामध्ये, फेज व्होल्टेज रूट 3 लाइन व्होल्टेजने गुणाकार केला जातो ज्यामुळे मशीनचा वेग कमी वेगाने चालतो ... ई डेल्टामध्ये, फेज व्होल्टेज लाइन व्होल्टेजच्या बरोबरीने असते ज्यामुळे मशीन हाय वेगाने चालते. तटस्थ सेवा प्रवेशद्वारावर ग्राऊंड केले जाते. आपल्याकडे सिंगल फेज लोड आहे तेथे वाई सिस्टम वापरणे आवश्यक आहे जे आपण फीड केले पाहिजे. विशेष म्हणजे, जर आपण तटस्थ लपवले तर आपण खरोखर स्टार आणि डेल्टा सिस्टममधील फरक सांगू शकत नाही. फेज-टू-फेज व्होल्टेज अगदी समान आहे.
वाई कनेक्शन ही सामान्यत: चार-वायर प्रणाली असते, ज्यात तीन लाइन कंडक्टर आणि एक तटस्थ कंडक्टर असतात, तर डेल्टा कनेक्शन ही तीन-वायर प्रणाली असते, ज्यात तीन लाइन कंडक्टर असतात.