DSE6010 MKII & DSE6020 MKII Operator Manual · DSE6010 MKII & DSE6020 MKII Operator Manual ... No...
057-230 IS 057-230 ISSUE: 1 DEEP SEA ELECTRONICS PLC DSE6010 MKII & DSE6020 MKII Operator Manual Document Number: 057-230 Author: Mark Graham
DSE6010 MKII & DSE6020 MKII Operator Manual · DSE6010 MKII & DSE6020 MKII Operator Manual ... No part of this publication may be reproduced in any ... DSE Part Description 057-004
trinhcong
Text of DSE6010 MKII & DSE6020 MKII Operator Manual · DSE6010 MKII & DSE6020 MKII Operator Manual ... No...
057-230 IS 057-230 ISSUE: 1
DEEP SEA ELECTRONICS PLC DSE6010 MKII & DSE6020 MKII Operator
Document Number: 057-230
Author: Mark Graham
057-230 ISSUE: 1 Page 2 of 100
DEEP SEA ELECTRONICS PLC Highfield House Hunmanby North Yorkshire YO14 0PH ENGLAND Sales Tel: +44 (0) 1723 890099 Sales Fax: +44 (0) 1723 893303 E-mail: [email protected] Website: www.deepseaplc.com
DSE6010 MKII & DSE6020 MKII Operator Manual Deep Sea Electronics Plc All rights reserved. No part of this publication may be reproduced in any material form (including photocopying or storing in any medium by electronic means or other) without the written permission of the copyright holder except in accordance with the provisions of the Copyright, Designs and Patents Act 1988. Applications for the copyright holders written permission to reproduce any part of this publication should be addressed to Deep Sea Electronics Plc at the address above. The DSE logo is a UK registered trademarks of Deep Sea Electronics PLC. Any reference to trademarked product names used within this publication is owned by their respective companies. Deep Sea Electronics Plc reserves the right to change the contents of this document without prior notice.
Amendments List
Issue Comments
Version Required
Configuration Suite
Version required 1 Initial release V 1.0.0 2014.103 V 2.17.3
Typeface: The typeface used in this document is Arial. Care should be taken not to mistake the upper case letter I with the numeral 1. The numeral 1 has a top serif to avoid this confusion.
Clarification of notation used within this publication.
NOTE Highlights an essential element of a procedure to ensure correctness.
CAUTION! Indicates a procedure or practice, which, if not strictly observed, could
result in damage or destruction of equipment.
WARNING! Indicates a procedure or practice, which could result in injury to personnel
or loss of life if not followed correctly.
Page 3 of 100 057-230 ISSUE: 1
1 INTRODUCTION .............................................................................................. 7 1.1 BIBLIOGRAPHY ..................................................................................................................8
1.1.1 INSTALLATION INSTRUCTIONS .................................................................................8 1.1.2 TRAINING GUIDES .......................................................................................................8 1.1.3 MANUALS .....................................................................................................................8 1.1.4 THIRD PARTY DOCUMENTS ......................................................................................8
2 SPECIFICATION .............................................................................................. 9 2.1 SHORT NAMES ...................................................................................................................9 2.2 OPERATING TEMPERATURE ............................................................................................9
2.2.1 SCREEN HEATER OPERATION ..................................................................................9 2.3 REQUIREMENTS FOR UL CERTIFICATION .....................................................................9 2.4 TERMINAL SPECIFICATION.............................................................................................10 2.5 POWER SUPPLY REQUIREMENTS .................................................................................10
2.5.1 MODULE SUPPLY INSTRUMENTATION DISPLAY ..................................................10 2.6 VOLTAGE & FREQUENCY SENSING ..............................................................................11 2.7 CURRENT SENSING .........................................................................................................11
2.7.1 VA RATING OF THE CTS ...........................................................................................12 2.7.2 CT POLARITY .............................................................................................................13 2.7.3 CT PHASING ...............................................................................................................13 2.7.4 CT CLASS ...................................................................................................................13
2.8 INPUTS ...............................................................................................................................14 2.8.1 DIGITAL INPUTS ........................................................................................................14 2.8.2 ANALOGUE INPUTS ..................................................................................................14
2.8.2.1 OIL PRESSURE ...................................................................................................14 2.8.2.2 COOLANT TEMPERATURE ................................................................................14 2.8.2.3 FUEL LEVEL SENSOR ........................................................................................15 2.8.2.4 FLEXIBLE SENSOR ............................................................................................15
2.8.2.4.1 RESISTIVE CONFIGURATION ........................................................................15 2.8.2.4.2 0-10V INPUT CONFIGURATION ....................................................................15 2.8.2.4.3 4-20 MA INPUT CONFIGURATION .................................................................15
2.8.3 CHARGE FAIL INPUT .................................................................................................16 2.8.4 MAGNETIC PICKUP ...................................................................................................17
2.9 OUTPUTS ...........................................................................................................................17 2.9.1 DC OUTPUTS A & B (FUEL & START) ......................................................................17 2.9.2 CONFIGURABLE DC OUTPUTS C, D, E & F ............................................................17
2.10 COMMUNICATION PORTS ...........................................................................................18 2.10.1 CAN INTERFACE .......................................................................................................18 2.10.2 USB CONNECTION ....................................................................................................19
2.11 ADDING AN EXTERNAL SOUNDER .............................................................................20 2.12 ACCUMULATED INSTRUMENTATION ........................................................................20 2.13 DIMENSIONS AND MOUNTING ....................................................................................21
2.13.1 DIMENSIONS ..............................................................................................................21 2.13.2 PANEL CUTOUT .........................................................................................................21 2.13.3 WEIGHT ......................................................................................................................21 2.13.4 FIXING CLIPS .............................................................................................................22 2.13.5 SILICON SEALING GASKET ......................................................................................23 2.13.6 APPLICABLE STANDARDS .......................................................................................24 2.13.7 ENCLOSURE CLASSIFICATIONS .............................................................................26
2.13.7.1 IP CLASSIFICATIONS .........................................................................................26 2.13.7.2 NEMA CLASSIFICATIONS ..................................................................................27
3 INSTALLATION ............................................................................................. 28 3.1 TERMINAL DESCRIPTION ................................................................................................28
3.1.1 DC SUPPLY, ESTOP INPUT, DC OUTPUTS & CHARGE FAIL INPUT ....................29 3.1.2 ANALOGUE SENSORS, MPU & CAN ........................................................................30
3.1.3 GENERATOR / MAINS VOLTAGE & FREQUENCY SENSING .................................31 3.1.4 CURRENT TRANSFORMERS ....................................................................................31
3.1.4.1 CT CONNECTIONS .............................................................................................32 3.1.5 CONFIGURABLE DIGITAL INPUTS ...........................................................................32 3.1.6 PC CONFIGURATION INTERFACE CONNECTOR ..................................................33
3.2 TYPICAL WIRING DIAGRAM ............................................................................................34 3.2.1 DSE6010 MKII TYPICAL WIRING DIAGRAM (3 PHASE 4 WIRE) ............................35 3.2.2 DSE6020 MKII TYPICAL WIRING DIAGRAM (3 PHASE 4 WIRE) ............................36
3.3 ALTERNATE TOPOLOGY WIRING DIAGRAMS ..............................................................37 3.3.1 GENERATOR ..............................................................................................................37 3.3.2 MAINS (6020 MKII ONLY) ...........................................................................................38
3.4 EARTH SYSTEMS .............................................................................................................39 3.4.1 NEGATIVE EARTH .....................................................................................................39 3.4.2 POSITIVE EARTH .......................................................................................................39 3.4.3 FLOATING EARTH .....................................................................................................39
4 DESCRIPTION OF CONTROLS .................................................................... 40 4.1 DSE6010 MKII ....................................................................................................................41 4.2 DSE6020 MKII ....................................................................................................................42 4.3 CONTROL PUSH-BUTTONS ............................................................................................43 4.4 MODULE DISPLAY ............................................................................................................46
4.4.1 BACKLIGHT ................................................................................................................47 4.4.2 INSTRUMENTATION ICONS .....................................................................................47 4.4.3 ACTIVE CONFIGURATION ........................................................................................48 4.4.4 FRONT PANEL EDITOR (FPE) / AUTO RUN ICON ..................................................48 4.4.5 MODE ICON ................................................................................................................48 4.4.6 ALARM ICONS (PROTECTIONS) ..............................................................................49
4.4.6.1 WARNING ALARM ICONS ..................................................................................50 4.4.6.2 ELECTRICAL TRIP ALARM ICONS ....................................................................51 4.4.6.3 SHUTDOWN ALARM ICONS ..............................................................................52
4.5 VIEWING THE INSTRUMENT PAGES ..............................................................................54 4.5.1 NAVIGATION MENU ...................................................................................................54
4.5.1.1 NAVIGATION MENU ICONS ...............................................................................54 4.5.2 GENERAL NAVIGATION ............................................................................................55 4.5.3 HOME ..........................................................................................................................56 4.5.4 GENERATOR ..............................................................................................................56 4.5.5 MAINS (DSE6020 MKII ONLY) ...................................................................................57 4.5.6 LOAD ...........................................................................................................................57 4.5.7 ENGINE .......................................................................................................................58 4.5.8 INFO ............................................................................................................................58 4.5.9 ENGINE DTC (ECU ALARMS) ....................................................................................59
4.5.9.1 VIEWING ACTIVE ENGINE DTC ........................................................................59 4.5.10 EVENT LOG ................................................................................................................61
4.5.10.1 VIEWING THE EVENT LOG ................................................................................62
5 OPERATION .................................................................................................. 63 5.1 QUICKSTART GUIDE ........................................................................................................63
5.1.1 STARTING THE ENGINE ...........................................................................................63 5.1.2 STOPPING THE ENGINE ...........................................................................................64
5.2 STOP/RESET MODE .........................................................................................................65 5.3 MANUAL MODE .................................................................................................................66
5.3.1 STARTING SEQUENCE .............................................................................................66 5.3.2 ENGINE RUNNING .....................................................................................................67 5.3.3 STOPPING SEQUENCE .............................................................................................67
5.4 TEST MODE .......................................................................................................................68 5.4.1 STARTING SEQUENCE .............................................................................................68 5.4.2 ENGINE RUNNING .....................................................................................................69 5.4.3 STOPPING SEQUENCE .............................................................................................69
5.5 AUTOMATIC MODE .........................................................................................................70 5.5.1 WAITING IN AUTO MODE .........................................................................................70 5.5.2 STARTING SEQUENCE .............................................................................................70
5.5.3 ENGINE RUNNING .....................................................................................................71 5.5.4 STOPPING SEQUENCE .............................................................................................71
5.6 MAINTENANCE ALARM ....................................................................................................72 5.7 SCHEDULER......................................................................................................................73
5.7.1 STOP MODE ...............................................................................................................73 5.7.2 MANUAL MODE ..........................................................................................................73 5.7.3 TEST MODE ................................................................................................................73 5.7.4 AUTO MODE ...............................................................................................................73
6 FRONT PANEL CONFIGURATION ............................................................... 74 6.1 ACCESSING THE FRONT PANEL CONFIGURATION EDITOR ......................................75 6.2 ADJUSTABLE PARAMETERS ..........................................................................................76
6.2.1 MODULE SETTINGS ..................................................................................................76 6.2.2 CAN SETTINGS ..........................................................................................................76 6.2.3 INPUT SETTINGS .......................................................................................................77 6.2.4 OUTPUT SETTINGS ...................................................................................................78 6.2.5 TIMER SETTINGS ......................................................................................................78 6.2.6 GENERATOR SETTINGS ...........................................................................................79 6.2.7 MAINS SETTINGS ......................................................................................................80 6.2.8 ENGINE SETTINGS ....................................................................................................81 6.2.9 ANALOGUE INPUTS SETTINGS ...............................................................................82 6.2.10 SCHEDULER SETTINGS ...........................................................................................84 6.2.11 TIME AND DATE SETTINGS ......................................................................................84 6.2.12 MAINTENANCE ALARM SETTINGS ..........................................................................85 6.2.13 ALTERNATE CONFIGURATION SETTINGS .............................................................85
6.3 SELECTABLE PARAMETER SETTINGS .........................................................................87 6.3.1 INPUT SOURCES .......................................................................................................87 6.3.2 OUTPUT SOURCES ...................................................................................................88 6.3.3 ALARM ACTION ..........................................................................................................90 6.3.4 FLEXIBLE SENSOR ALARM ACTION ........................................................................90 6.3.5 POWER UP MODE .....................................................................................................90 6.3.6 SENSOR TYPE ...........................................................................................................90 6.3.7 AC SYSTEM ................................................................................................................90 6.3.8 DIGITAL INPUT ALARM ARMING ..............................................................................91 6.3.9 DIGITAL INPUT POLARITY ........................................................................................91 6.3.10 DIGITAL OUTPUT POLARITY ....................................................................................91 6.3.11 FUEL UNITS ................................................................................................................91 6.3.12 PRESSURE SENSOR LIST ........................................................................................92 6.3.13 TEMPERATURE SENSOR LIST.................................................................................92 6.3.14 PERCENTAGE SENSOR LIST ...................................................................................92
7 COMMISSIONING ......................................................................................... 93
8 FAULT FINDING ............................................................................................ 94 8.1 STARTING..........................................................................................................................94 8.2 LOADING ...........................................................................................................................94 8.3 ALARMS .............................................................................................................................95 8.4 COMMUNICATIONS ..........................................................................................................95 8.5 INSTRUMENTS ..................................................................................................................95 8.6 MISCELLANEOUS .............................................................................................................96
9 MAINTENANCE, SPARES, REPAIR AND SERVICING ................................ 97 9.1 PURCHASING ADDITIONAL CONNECTOR PLUGS FROM DSE ...................................97
9.1.1 PACK OF PLUGS ........................................................................................................97 9.1.2 INDIVIDUAL PLUGS ...................................................................................................97
9.2 PURCHASING ADDITIONAL FIXING CLIPS FROM DSE ................................................97 9.3 PURCHASING ADDITIONAL SEALING GASKET FROM DSE ........................................97
10 WARRANTY ................................................................................................ 98
11 DISPOSAL .................................................................................................. 98
11.1 WEEE (WASTE ELECTRICAL AND ELECTRONIC EQUIPMENT) ..............................98
1 INTRODUCTION This document details the installation and operation requirements of the DSE6010 MKII & DSE6020 MKII modules, part of the DSEGenset range of products.
The manual forms part of the product and should be kept for the entire life of the product. If the product is passed or supplied to another party, ensure that this document is passed to them for reference purposes. This is not a controlled document. DSE do not automatically inform on updates. Any future updates of this document are included on the DSE website at www.deepseaplc.com The DSE60xx MKII series is designed to provide differing levels of functionality across a common platform. This allows the generator OEM greater flexibility in the choice of controller to use for a specific application.
The DSE60xx MKII series module has been designed to allow the operator to start and stop the generator, and if required, transfer the load to the generator either manually or automatically. Additionally, the DSE6020 MKII automatically starts and stops the generator set depending upon the status of the mains (utility) supply. The user also has the facility to view the system operating parameters via the LCD display.
The DSE60xx MKII module monitors the engine, indicating the operational status and fault conditions, automatically shutting down the engine and giving a true first up fault condition of an engine failure by the LCD display.
The powerful ARM microprocessor contained within the module allows for incorporation of a range of complex features:
Icon based LCD display
True RMS Voltage
Current and Power monitoring
USB Communications
Engine parameter monitoring.
Fully configurable inputs for use as alarms or a range of different functions.
Engine ECU interface to electronic engines. Using a PC and the DSE Configuration Suite software allows alteration of selected operational sequences, timers, alarms and operational sequences. Additionally, the modules integral front panel configuration editor allows adjustment of this information. A robust plastic case designed for front panel mounting houses the module. Connections are via locking plug and sockets. Access to critical operational sequences and timers for use by qualified engineers, can be protected by a security code. Module access can also be protected by PIN code. Selected parameters can be changed from the modules front panel. The module is housed in a robust plastic case suitable for panel mounting. Connections to the module are via locking plug and sockets.
1.1 BIBLIOGRAPHY
This document refers to and is referred to by the following DSE publications which can be obtained from the DSE website: www.deepseaplc.com
1.1.1 INSTALLATION INSTRUCTIONS Installation instructions are supplied with the product in the box and are intended as a quick start guide only.
DSE Part Description
053-174 DSE6010 MKII & DSE6020 MKII Installation Instructions
1.1.2 TRAINING GUIDES Training Guides are produced to give handout sheets on specific subjects during training sessions
056-005 Using CTs With DSE Products
056-010 Over Current Protection
056-022 Breaker Control
056-029 Smoke Limiting
056-030 Module PIN Codes
1.1.3 MANUALS Product manuals are can be downloaded from the DSE website: www.deepseaplc.com
057-004 Electronic Engines and DSE Wiring Guide
057-223 DSE6010 MKII & DSE6020 MKII Configuration Suite PC Software Manual
1.1.4 THIRD PARTY DOCUMENTS The following third party documents are also referred to:
ISBN 1-55937-879-4 IEEE Std C37.2-1996 IEEE Standard Electrical Power System Device Function Numbers and Contact Designations. Institute of Electrical and Electronics Engineers Inc
ISBN 0-7506-1147-2 Diesel generator handbook. L.L.J. Mahon
ISBN 0-9625949-3-8 On-Site Power Generation. EGSA Education Committee.
2 SPECIFICATION
2.1 SHORT NAMES
Short Name Description
DSE6000,DSE6xxx MKII All modules in the DSE6000 MKII range.
DSE6000,DSE60xx MKII All modules in the DSE6000 MKII range.
DSE6010 MKII DSE6010 MKII module/controller
2.2 OPERATING TEMPERATURE
Module Description
DSE60xx MKII -30 C +70 C (-22 F +158 F )
Display Heater Variants -40 C +70 C (-40 F +158 F )
2.2.1 SCREEN HEATER OPERATION
Screen Heater Function Description
Turn On When Temperature Falls Below -10 C (+14 F)
Turn Off When Temperature Rises Above -5 C (+23 F)
2.3 REQUIREMENTS FOR UL CERTIFICATION
Screw Terminal Tightening Torque
4.5 lb-in (0.5 Nm)
Terminals suitable for connection of conductor size 12 AWG 26 AWG (0.5mm to 2.0mm).
Conductor protection must be provided in accordance with NFPA 70, Article 240
Low voltage circuits (35 volts or less) must be supplied from the engine starting battery or an isolated secondary circuit.
The communication, sensor, and/or battery derived circuit conductors shall be separated and secured to maintain at least (6mm) separation from the generator and mains connected circuit conductors unless all conductors are rated 600 Volts or greater.
Current Inputs Must be connected through UL Listed or Recognized isolating current transformers with the secondary rating of 5A max.
Communication Circuits
Must be connected to communication circuits of UL Listed equipment
Output Pilot Duty 0.5 A
Suitable for use in type 1 Enclosure Type rating with surrounding air temperature -22 F to +158 F (-30 C to +70 C)
Suitable for pollution degree 3 environments when voltage sensing inputs do not exceed 300V. When used to monitor voltages over 300V device to be install in an unventilated or filtered ventilation enclosure to maintain a pollution degree 2 environment.
-22 F to +158 F (-30 C to +70 C)
057-230 ISSUE: 1 Page 10 of 100
2.4 TERMINAL SPECIFICATION
NOTE: For purchasing additional connector plugs from DSE, please see the section
entitled Maintenance, Spares, Repair and Servicing elsewhere in this document.
Two part connector.
Male part fitted to module
Female part supplied in module packing case - Screw terminal, rising clamp, no internal spring.
Example showing cable entry and screw terminals of a 10 way connector
Minimum Cable Size 0.5 mm (AWG 24)
Maximum Cable Size 2.5 mm (AWG 10)
2.5 POWER SUPPLY REQUIREMENTS
Minimum Supply Voltage 8 V continuous
Cranking Dropouts Able to survive 0 V for 100 ms providing the supply was at least 10 V before the dropout and recovers to 5 V afterwards.
Maximum Supply Voltage 35 V continuous (60 V protection)
Reverse Polarity Protection -35 V continuous
Maximum Operating Current 100 mA at 12 V 105 mA at 24 V
Maximum Standby Current 60 mA at 12 V 55 mA at 24 V
Maximum Current When In Sleep Mode
40 mA at 12 V 35 mA at 24 V
Typical Power (Controller On, Heater Off)
1.2 W to 2.4 W
Typical Power (Controller In Standby, Heater Off)
2.5.1 MODULE SUPPLY INSTRUMENTATION DISPLAY
Range 0 V to 70 V DC (note Maximum continuous operating voltage of 35 V DC)
Resolution 0.1 V
Accuracy 1 % full scale (0.7 V)
Page 11 of 100 057-230 ISSUE: 1
2.6 VOLTAGE & FREQUENCY SENSING
Measurement Type True RMS conversion
Sample Rate 5 kHz or better
Harmonics Up to 11th or better
Input Impedance 300 k phase to neutral
Phase To Neutral
15 V (minimum required for sensing frequency) to 415 V AC (absolute maximum)
Suitable for 345 V AC nominal (20 % for under/overvoltage detection)
Phase To Phase
Common Mode Offset From Earth 100 V AC (max)
Resolution 1 V AC phase to neutral 2 V AC phase to phase
Accuracy 1 % of full scale phase to neutral 2 % of full scale phase to phase
Minimum Frequency 3.5 Hz
Maximum Frequency 75.0 Hz
Frequency Resolution 0.1 Hz
Frequency Accuracy 0.2 Hz
2.7 CURRENT SENSING
Nominal CT Secondary Rating 5 A
Maximum Continuous Current 5 A
Overload Measurement 3 x Nominal Range setting
Absolute Maximum Overload 50 A for 1 second
Burden 0.25 VA (0.01 current shunts)
Common Mode Offset 1 V peak plant ground to CT common terminal
Resolution 0.5 % of 5 A
Accuracy 1 % of Nominal (5 A) (excluding CT error)
2.7.1 VA RATING OF THE CTS
: Details for 4 mm cables are shown for reference only. The connectors on the DSE modules
are only suitable for cables up to 2.5 mm.
The VA burden of the module on the CTs is 0.5 VA. However depending upon the type and length of cabling between the CTs and the module, CTs with a greater VA rating than the module are required. The distance between the CTs and the measuring module should be estimated and cross-referenced against the chart opposite to find the VA burden of the cable itself. If the CTs are fitted within the alternator top box, the star point (common) of the CTs should be connected to system ground (earth) as close as possible to the CTs. This minimises the length of cable used to connect the CTs to the DSE module. Example. If 1.5 mm cable is used and the distance from the CT to the measuring module is 20 m, then the burden of the cable alone is approximately 15 VA. As the burden of the DSE controller is 0.5 VA, then a CT with a rating of at least 15 + 0.5 V = 15.5 VA must be used. If 2.5 mm cables are used over the same distance of 20 m, then the burden of the cable on the CT is approximately 7 VA. CTs required in this instance is at least 7.5 VA (7+0.5).
2.7.2 CT POLARITY
NOTE: Take care to ensure correct polarity of the CT primary as shown above. If in doubt,
check with the CT supplier.
Take care to ensure the correct polarity of the CTs. Incorrect CT orientation leads to negative kW readings when the set is supplying power. Take note that paper stick-on labels on CTs that show the orientation are often incorrectly placed on the CT (!). It is more reliable to use the labelling in the case moulding as an indicator to orientation (if available). To test orientation, run the generator in island mode (not in parallel with any other supply) and load the generator to around 10 % of the set rating. Ensure the DSE module shows positive kW for all three individual phase readings.
TO GENERATOR
TO LOAD
POLARITY OF CT PRIMARY
2.7.3 CT PHASING Take particular care that the CTs are connected to the correct phases. For instance, ensure that the CT on phase 1 is connected to the terminal on the DSE module intended for connection to the CT for phase 1. Additionally ensure that the voltage sensing for phase 1 is actually connected to generator phase 1. Incorrect connection of the phases as described above results in incorrect power factor (pf) measurements, which in turn results in incorrect kW measurements. One way to check for this is to make use of a single-phase load. Place the load on each phase in turn, run the generator and ensure the kW value appears in the correct phase. For instance if the load is connected to phase 3, ensure the kW figure appears in phase 3 display and not in the display for phase 1 or 2.
2.7.4 CT CLASS Ensure the correct CT type is chosen. For instance if the DSE module is providing overcurrent protection, ensure the CT is capable of measuring the overload level you wish to protect against, and at the accuracy level you require. For instance, this may mean fitting a protection class CT (P10 type) to maintain high accuracy while the CT is measuring overload currents. Conversely, if the DSE module is using the CT for instrumentation only (current protection is disabled or not fitted to the controller), then measurement class CTs can be used. Again, bear in mind the accuracy you require. The DSE module is accurate to better than 1% of the full-scale current reading. To maintain this accuracy you should fit Class 0.5 or Class 1 CTs. You should check with your CT manufacturer for further advice on selecting your CTs
Labelled as
p1, k or K
p2, l or L
2.8 INPUTS
2.8.1 DIGITAL INPUTS
Number 6 configurable digital inputs (10 when Analogue Inputs are configured as digital inputs)
Arrangement Contact between terminal and ground
Low Level Threshold 3.2 V minimum
High Level Threshold 8.1 V maximum
Maximum Input Voltage +60 V DC with respect to plant supply negative
Minimum Input Voltage -24 V DC with respect to plant supply negative
Contact Wetting Current 6 mA typical
Open Circuit Voltage 15 V typical
2.8.2 ANALOGUE INPUTS
2.8.2.1 OIL PRESSURE
Measurement Type Resistance measurement by measuring voltage across sensor with a fixed current applied
Arrangement Differential resistance measurement input
Measurement Current 11 mA 10 %
Full Scale 240
Over Range / Fail 270
Resolution 0.1 Bar (1-2 PSI)
Accuracy 2 % of full scale resistance (4.8 ) excluding transducer error
Max Common Mode Voltage 2 V
Display Range 0 bar to 17.2 bar (0 PSI to 250 PSI) subject to limits of the sensor
2.8.2.2 COOLANT TEMPERATURE
Resolution 1 C (2 F)
Accuracy +/-2 % of full scale resistance (9.6 ) excluding transducer error
Display Range 0 C to 250 C (32 F to 482 F) subject to limits of the sensor
2.8.2.3 FUEL LEVEL SENSOR
Resolution 1 %
Display Range 0 % to 250 % subject to limits of the sensor
2.8.2.4 FLEXIBLE SENSOR
2.8.2.4.1 RESISTIVE CONFIGURATION
Number 2 when Fuel Level Sender is configured as a flexible
Display Range 0 % to 250 %, 0 C to 250 C (32 F to 482 F) or 0 bar to 17.2 bar (0 PSI to 250 PSI)subject to limits of the sensor and sensor configuration
2.8.2.4.2 0-10V INPUT CONFIGURATION
Number 1 configurable ratiometric input
Full Scale 0 V to 10 V
Resolution 1%
Accuracy +/-2% of full scale voltage (0.2 V) excluding transducer error
Display Range 0% to 250%, -200 C to 1300 C (-328 F to 2372 F) or 0 bar to 17.2 bar (0 PSI to 250 PSI) subject to limits of the sensor and sensor configuration
2.8.2.4.3 4-20 MA INPUT CONFIGURATION
Full Scale 0 mA to 20 mA
Accuracy +/-2% of full scale resistance (0.4 mA) excluding transducer error
Display Range 00% to 250%, -200 C to 1300 C (-328 F to 2372 F) or 0 bar to 17.2 bar (0 PSI to 250 PSI) subject to limits of the sensor and sensor configuration
2.8.3 CHARGE FAIL INPUT
Minimum Voltage 0 V
Maximum Voltage 35 V (plant supply)
Accuracy 1 % of max measured voltage
Excitation Active circuit constant power output
Output Power 2.5 W nominal at 12 V and 24 V
Current At 12V 210 mA
The charge fail input is actually a combined input and output. Whenever the generator is required to run, the terminal provides excitation current to the charge alternator field winding. When the charge alternator is correctly charging the battery, the voltage of the terminal is close to the plant battery supply voltage. In a failed charge situation, the voltage of this terminal is pulled down to a low voltage. It is this drop in voltage that triggers the Charge Failure alarm. The level at which this operates and whether this triggers a warning or shutdown alarm is configurable using the DSE Configuration Suite Software.
2.8.4 MAGNETIC PICKUP
NOTE: DSE can supply a suitable magnetic pickup device, available in two body thread
lengths:
DSE Part number 020-012 - Magnetic Pickup probe 5/8 UNF 2 thread length
Type Differential input
Minimum Voltage 0.5 V RMS
Maximum Voltage Clamped to 70 V by transient suppressers, dissipation not to exceed1 W.
Maximum Frequency 10,000 Hz
Resolution 6.25 RPM
Accuracy 25 RPM
Flywheel Teeth 10 to 500
Magnetic Pickup devices can often be shared between two or more devices. For example, one device can often supply the signal to both the DSE module and the engine governor. The possibility of this depends upon the amount of current that the magnetic pickup can supply.
2.9 OUTPUTS
2.9.1 DC OUTPUTS A & B (FUEL & START)
Type Normally used as Fuel & Start outputs. Fully configurable for other purposes if the module is configured to control an electronic engine.
Rating 10 A resistive for 10 secs, 5 A resistive continuous at 35 V
2.9.2 CONFIGURABLE DC OUTPUTS C, D, E & F
Type Fully configurable, supplied from DC supply terminal 2.
Rating 2 A resistive continuous at 35 V
2.10 COMMUNICATION PORTS
USB Port USB 2.0 Device for connection to PC running DSE configuration suite only. Max distance 6m (18 yards)
CAN Port
NOTE: For additional length, the DSE124 CAN Extender is available. For
more information, refer to DSE Publication: 057-116 DSE124 Operator Manual
Engine CAN Port Standard implementation of Slow mode, up to 250 K bits/s Non-Isolated.
Internal Termination provided (120 ) Max distance 40 m (133 feet)
2.10.1 CAN INTERFACE
NOTE: For further details on connection to electronic engines, refer to DSE Publication:
057-004 Electronic Engines And DSE Wiring
Modules are fitted with the CAN interface as standard and are capable of receiving engine data from engine CAN controllers compliant with the CAN standard. CAN enabled engine controllers monitor the engines operating parameters such as engine speed, oil pressure, engine temperature
(among others) in order to closely monitor and control the engine. The industry standard communications interface (CAN) transports data gathered by the engine controller interface. This allows generator controllers to access these engine parameters with no physical connection to the sensor device.
2.10.2 USB CONNECTION
NOTE: The DC supply must be connected to the module for configuration by PC.
NOTE: For further details of module configuration, refer to DSE Publication: 057-223
DSE60xx MKII Configuration Software Manual.
The USB port is provided to give a simple means of connection between a PC and the controller. Using the DSE Configuration Suite Software, the operator is then able to control the module, starting or stopping the generator, selecting operating modes, etc. Additionally, the various operating parameters (such as output volts, oil pressure, etc.) of the remote generator are available to be viewed or changed. To connect a module to a PC by USB, the following items are required:
DSE6010 MKII & DSE6020 MKII Controller
DSE Configuration Suite PC Software (Supplied on configuration suite software CD or available from www.deepseaplc.com).
USB cable Type A to Type B. (This is the same cable as often used between a PC and a USB printer) DSE can supply this cable if required : PC Configuration interface lead (USB type A type B) DSE Part No 016-125
2.11 ADDING AN EXTERNAL SOUNDER Should an external alarm or indicator be required, this can be achieved by using the DSE Configuration Suite PC software to configure an auxiliary output for Audible Alarm, and by configuring an auxiliary input for Alarm Mute (if required). The audible alarm output activates and de-activates at the same time as the modules internal
sounder. The Alarm mute input and internal Lamp Test / Alarm Mute button activate in parallel with each other. Either signal mutes both the internal sounder and audible alarm output. Example of configuration to achieve external sounder with external alarm mute button:
2.12 ACCUMULATED INSTRUMENTATION
NOTE: When an accumulated instrumentation value exceeds the maximum number as
listed below, the value is reset and begins counting from zero again.
Engine Hours Run Maximum 99999 hrs 59 minutes (Approximately 11yrs 4 months)
Accumulated Power 999999 kWh / kVArh / kVAh
The number of logged Engine Hours and Number of Starts can be set/reset using the DSE Configuration Suite PC software. Depending upon module configuration, this may have been PIN number locked by your generator supplier
2.13 DIMENSIONS AND MOUNTING
2.13.1 DIMENSIONS 216 mm x 158 mm x 43 mm (8.5 x 6.2 x 1.5)
2.13.2 PANEL CUTOUT 184 mm x 137 mm (7.2 x 5.3)
2.13.3 WEIGHT 0.45 kg (1.00 lb)
2.13.4 FIXING CLIPS
NOTE: In conditions of excessive vibration, mount the module on suitable anti-vibration
mountings.
The module is held into the panel fascia using the supplied fixing clips.
Withdraw the fixing clip screw (turn anticlockwise) until only the pointed end is protruding from the clip.
Insert the three prongs of the fixing clip into the slots in the side of the module case.
Pull the fixing clip backwards (towards the back of the module) ensuring all three prongs of the clip are inside their allotted slots.
Turn the fixing clip screws clockwise until they make contact with the panel fascia.
Turn the screws a little more to secure the module into the panel fascia. Care should be taken not to over tighten the fixing clip screws.
Fixing clip fitted to module
Fixing clip
2.13.5 SILICON SEALING GASKET
NOTE: For purchasing an additional silicon gasket from DSE, please see the section
The optional silicon gasket provides improved sealing between module and the panel fascia. The gasket is fitted to the module before installation into the panel fascia. Take care to ensure the gasket is correctly fitted to the module to maintain the integrity of the seal.
Gasket fitted to module
Sealing gasket
2.13.6 APPLICABLE STANDARDS
BS 4884-1 This document conforms to BS4884-1 1992 Specification for presentation of essential information.
BS 4884-2 This document conforms to BS4884-2 1993 Guide to content
BS 4884-3 This document conforms to BS4884-3 1993 Guide to presentation
BS EN 60068-2-1 (Minimum temperature)
-30 C (-22 F)
BS EN 60068-2-2 (Maximum temperature)
+70 C (158 F)
BS EN 60950 Safety of information technology equipment, including electrical business equipment
BS EN 61000-6-2 EMC Generic Immunity Standard (Industrial)
BS EN 61000-6-4 EMC Generic Emission Standard (Industrial)
BS EN 60529 (Degrees of protection provided by enclosures)
IP65 (front of module when installed into the control panel with the optional sealing gasket) IP42 (front of module when installed into the control panel WITHOUT being sealed to the panel)
NEMA rating (Approximate)
12 (Front of module when installed into the control panel with the optional sealing gasket). 2 (Front of module when installed into the control panel WITHOUT being sealed to the panel)
IEEE C37.2 (Standard Electrical Power System Device Function Numbers and Contact Designations)
Under the scope of IEEE 37.2, function numbers can also be used to represent functions in microprocessor devices and software programs. The controller is device number 11L-8000 (Multifunction device protecting Line (generator) module). As the module is configurable by the generator OEM, the functions covered by the module vary. Under the modules factory configuration, the device numbers included within the module are : 2 Time Delay Starting Or Closing Relay 3 Checking Or Interlocking Relay 5 Stopping Device 6 Starting Circuit Breaker 8 Control Power Disconnecting Device 10 Unit Sequence Switch 11 Multifunction Device 12 Overspeed Device 14 Underspeed Device 26 Apparatus Thermal Device 27AC AC Undervoltage Relay 27DC DC Undervoltage Relay 29 Isolating Contactor Or Switch 30 Annunciator Relay 31 Separate Excitation Device 42 Running Circuit Breaker
Continued overleaf...
Continued 50 Instantaneous Overcurrent Relay 52 AC Circuit Breaker 53 Exciter Or DC Generator Relay 54 Turning Gear Engaging Device 59AC AC Overvoltage Relay 59DC DC Overvoltage Relay 62 Time Delay Stopping Or Opening Relay 63 Pressure Switch 71 Level Switch 74 Alarm Relay 81 Frequency Relay 83 Automatic Selective Control Or Transfer Relay 86 Lockout Relay
In line with our policy of continual development, Deep Sea Electronics, reserve the right to change specification without notice.
2.13.7 ENCLOSURE CLASSIFICATIONS
2.13.7.1 IP CLASSIFICATIONS The modules specification under BS EN 60529 Degrees of protection provided by enclosures
IP65 (Front of module when module is installed into the control panel with the optional sealing gasket).
IP42 (front of module when module is installed into the control panel WITHOUT being sealed to the panel)
First Digit Second Digit
Protection against contact and ingress of solid objects Protection against ingress of water
0 No protection 0 No protection
1 Protected against ingress solid objects with a diameter of more than 50 mm. No protection against deliberate access, e.g. with a hand, but large surfaces of the body are prevented from approach.
1 Protection against dripping water falling vertically. No harmful effect must be produced (vertically falling drops).
2 Protected against penetration by solid objects with a diameter of more than 12 mm. Fingers or similar objects prevented from approach.
2 Protection against dripping water falling vertically. There must be no harmful effect when the equipment (enclosure) is tilted at an angle up to 15 from its normal position (drops falling at an angle).
3 Protected against ingress of solid objects with a diameter of more than 2.5 mm. Tools, wires etc. with a thickness of more than 2.5 mm are prevented from approach.
3 Protection against water falling at any angle up to 60 from the vertical. There must be no harmful effect (spray water).
4 Protected against ingress of solid objects with a diameter of more than 1 mm. Tools, wires etc. with a thickness of more than 1 mm are prevented from approach.
4 Protection against water splashed against the equipment (enclosure) from any direction. There must be no harmful effect (splashing water).
5 Protected against harmful dust deposits. Ingress of dust is not totally prevented but the dust must not enter in sufficient quantity to interface with satisfactory operation of the equipment. Complete protection against contact.
5 Protection against water projected from a nozzle against the equipment (enclosure) from any direction. There must be no harmful effect (water jet).
6 Protection against ingress of dust (dust tight). Complete protection against contact.
6 Protection against heavy seas or powerful water jets. Water must not enter the equipment (enclosure) in harmful quantities (splashing over).
2.13.7.2 NEMA CLASSIFICATIONS
THE MODULES NEMA RATING (APPROXIMATE)
12 (Front of module when module is installed into the control panel with the optional sealing gasket).
2 (front of module when module is installed into the control panel WITHOUT being sealed to the panel)
NOTE: There is no direct equivalence between IP / NEMA ratings. IP figures shown are
approximate only.
Provides a degree of protection against contact with the enclosure equipment and against a limited amount of falling dirt.
Provides a degree of protection against limited amounts of falling water and dirt.
Provides a degree of protection against windblown dust, rain and sleet; undamaged by the formation of ice on the enclosure.
Provides a degree of protection against rain and sleet:; undamaged by the formation of ice on the enclosure.
4 (X)
Provides a degree of protection against splashing water, windblown dust and rain, hose directed water; undamaged by the formation of ice on the enclosure. (Resist corrosion).
12/12K
Provides a degree of protection against dust, falling dirt and dripping non corrosive liquids.
Provides a degree of protection against dust and spraying of water, oil and non corrosive coolants.
057-230 ISSUE: 1 Page 28 of 100 -230 ISSUE: 1
3 INSTALLATION The module is designed to be mounted on the panel fascia. For dimension and mounting details, see the section entitled Specification, Dimension and mounting elsewhere in this document.
3.1 TERMINAL DESCRIPTION
NOTE: Availability of some terminals depends upon module version. Full details are given
in the section entitled Terminal Description elsewhere in this manual.
To aid user connection, icons are used on the rear of the module to help identify terminal functions. An example of this is shown below.
Terminals 1-10 Terminals 11-21
Terminals 25-32 Terminals 38-43
USB PC Configuration
Terminals 33-37 UL Ratings
3.1.1 DC SUPPLY, ESTOP INPUT, DC OUTPUTS & CHARGE FAIL INPUT
NOTE: When the module is configured for operation with an electronic engine, FUEL and
START output requirements may be different. For further details on connection to electronic
engines, refer to DSE Publication: 057-004 Electronic Engines And DSE Wiring
DSE6010 MKII & 6020 MKII Configuration Software Manual.
No Description Cable Size Notes
1 DC Plant Supply Input (Negative)
2.5 mm AWG 13
2 DC Plant Supply Input (Positive)
Supplies the module and DC Outputs A, B, C, D, E & F
3 Emergency Stop Input
Plant Supply Positive. Also supplies DC Outputs A & B. (Recommended Maximum Fuse 20A)
4 DC Output A (FUEL) 2.5 mm AWG 13
Plant Supply Positive from terminal 2. 10A for 10secs, 5A resistive continuous Fixed as FUEL relay if electronic engine is not configured.
5 DC Output B (START) 2.5 mm AWG 13
Plant Supply Positive from terminal 2. 10A for 10secs, 5A resistive continuous Fixed as START relay if electronic engine is not configured.
6 Charge Fail / Excite
Do not connect to ground (battery negative). If charge alternator is not fitted, leave this terminal disconnected.
7 DC Output C 1.0 mm AWG 18
Plant Supply Positive from terminal 2. 2 Amp rated.
8 DC Output D 1.0 mm AWG 18
9 DC Output E 1.0 mm AWG 18
10 DC Output F 1.0 mm AWG 18
3.1.2 ANALOGUE SENSORS, MPU & CAN
NOTE: It is VERY important that terminal 11 (sensor common) is soundly connected to an
earth point on the ENGINE BLOCK, not within the control panel, and must be a sound electrical
connection to the sensor bodies. This connection MUST NOT be used to provide an earth
connection for other terminals or devices. The simplest way to achieve this is to run a
SEPARATE earth connection from the system earth star point, to terminal 11 directly, and not
use this earth for other connections.
NOTE: If you use PTFE insulating tape on the sensor thread when using earth return
sensors, ensure you do not insulate the entire thread, as this prevents the sensor body from
being earthed via the engine block.
NOTE: Screened 120 impedance cable specified for use with CAN must be used for the
CAN link.
DSE stock and supply Belden cable 9841 which is a high quality 120 impedance cable
suitable for CAN use (DSE part number 016-030)
Size Notes
11 Sensor Common Return 0.5 mm AWG 20
Return Feed For Sensors
12 Oil Pressure Input 0.5 mm AWG 20
Connect To Oil Pressure Sensor
13 Coolant Temperature Input 0.5mm AWG 20
Connect To Coolant Temperature Sensor
14 Fuel Level Input 0.5 mm AWG 20
Connect To Fuel Level Sensor
15 Flexible Sensor Input 0.5 mm AWG 20
Connect To Additional Sensor (User Configurable)
18 Magnetic Pickup Positive 0.5 mm AWG 20
Connect To Magnetic Pickup Device
19 Magnetic Pickup Negative 0.5 mm AWG 20
20 Magnetic Pickup Screen Shield Connect To Ground At One End Only
19 CAN Port H 0.5 mm AWG 20
Use Only 120 CAN Approved Cable
20 CAN Port L 0.5 mm AWG 20
21 CAN Port Screen Shield Use Only 120 CAN Approved Cable
3.1.3 GENERATOR / MAINS VOLTAGE & FREQUENCY SENSING
NOTE: Terminals 29 to 32 not fitted to DSE6010 MKII
NOTE: The above table describes connections to a three phase, four wire alternator. For
alternative wiring topologies, please see the Alternate Topology Wiring Diagrams section of
this manual.
25 Generator L1 (U) Voltage Monitoring
Connect to generator L1 (U) output (AC) (Recommend 2A fuse)
26 Generator L2 (V) Voltage Monitoring
Connect to generator L2 (V) output (AC) (Recommend 2A fuse)
27 Generator L3 (W) Voltage Monitoring
Connect to generator L3 (W) output (AC) (Recommend 2A fuse)
28 Generator Neutral (N) Input 1.0 mm AWG 18
Connect to generator Neutral terminal (AC)
29 Mains L1 (R) Voltage Monitoring 1.0 mm AWG 18
Connect to Mains L1 (R) output (AC) (Recommend 2A fuse)
30 Mains L2 (S) Voltage Monitoring 1.0 mm AWG 18
Connect to Mains L2 (S) output (AC) (Recommend 2A fuse)
31 Mains L3 (T) Voltage Monitoring 1.0 mm AWG 18
Connect to Mains L3 (T) output (AC) (Recommend 2A fuse)
32 Mains Neutral (N) Input 1.0 mm AWG 18
Connect to Mains Neutral terminal (AC)
3.1.4 CURRENT TRANSFORMERS
WARNING!: Do not disconnect this plug when the CTs are carrying current. Disconnection
open circuits the secondary of the C.T.s and dangerous voltages may then develop. Always
ensure the CTs are not carrying current and the CTs are short circuit connected before making
or breaking connections to the module.
NOTE: The module has a burden of 0.5VA on the CT. Ensure the CT is rated for the burden
of the controller, the cable length being used and any other equipment sharing the CT. If in
doubt, consult your CT supplier.
33 CT Secondary for L1 2.5 mm AWG 13
Connect to s1 secondary of L1 monitoring CT
36 CT Common
Connect to s2 secondary of L1, L2 & L3 monitoring CTs and ground 37
3.1.4.1 CT CONNECTIONS p1, k or K is the primary of the CT that points towards the GENERATOR
p2, l or L is the primary of the CT that points towards the Load
s1 is the secondary of the CT that connects to the DSE Modules input for the CT measuring s2 is the secondary of the CT that should be commoned with the s2 connections of all the other CTs and connected to the CT common terminal of the module.
3.1.5 CONFIGURABLE DIGITAL INPUTS
38 Configurable Digital Input A 0.5 mm AWG 20
Switch To Negative
39 Configurable Digital Input B 0.5 mm AWG 20
40 Configurable Digital Input C 0.5 mm AWG 20
41 Configurable Digital Input D 0.5 mm AWG 20
42 Configurable Digital Input E 0.5 mm AWG 20
43 Configurable Digital Input F 0.5 mm AWG 20
3.1.6 PC CONFIGURATION INTERFACE CONNECTOR
NOTE: The USB connection cable between the PC and the module must not be extended
beyond 5m (yards). For distances over 5m, it is possible to use a third party USB extender.
Typically, they extend USB up to 50m. The supply and support of this type of equipment is
outside the scope of Deep Sea Electronics PLC.
CAUTION!: Care must be taken not to overload the PCs USB system by connecting more
than the recommended number of USB devices to the PC. For further information, consult your
PC supplier.
Socket for connection to PC with DSE Configuration Suite Software
This is a standard USB type A to type B connector.
3.2 TYPICAL WIRING DIAGRAM As every system has different requirements, these diagrams show only a TYPICAL system and do not intend to show a complete system. Genset manufacturers and panel builders may use these diagrams as a starting point; however, you are referred to the completed system diagram provided by your system manufacturer for complete wiring detail. Further wiring suggestions are available in the following DSE publications, available at www.deepseaplc.com to website members.
056-022 Breaker Control (Training guide)
3.2.1 DSE6010 MKII TYPICAL WIRING DIAGRAM (3 PHASE 4 WIRE)
3.3 ALTERNATE TOPOLOGY WIRING DIAGRAMS
3.3.1 GENERATOR
3.3.2 MAINS (6020 MKII ONLY)
3.4 EARTH SYSTEMS
3.4.1 NEGATIVE EARTH The typical wiring diagrams located within this document show connections for a negative earth system (the battery negative connects to Earth)
3.4.2 POSITIVE EARTH When using a DSE module with a Positive Earth System (the battery positive connects to Earth), the following points must be followed:
Follow the typical wiring diagram as normal for all sections EXCEPT the earth points
All points shown as Earth on the typical wiring diagram should connect to BATTERY NEGATIVE (not earth).
3.4.3 FLOATING EARTH Where neither the battery positive nor battery negative terminals are connected to earth the following points must to be followed
Description Of Controls
4 DESCRIPTION OF CONTROLS
CAUTION: The module may instruct an engine start event due to external influences.
Therefore, it is possible for the engine to start at any time without warning. Prior to performing
any maintenance on the system, it is recommended that steps are taken to remove the battery
and isolate supplies.
NOTE: The following descriptions detail the sequences followed by a module containing
the standard factory configuration. Always refer to your configuration source for the exact
sequences and timers observed by any particular module in the field.
Control of the module is via push buttons mounted on the front of the module with
Stop/Reset Mode , Manual Mode , Test Mode (DSE6020 MKII Only), Auto Mode and Start functions. For normal operation, these are the only controls which need to be operated. Details of their operation are provided later in this document.
4.1 DSE6010 MKII
Module Display
Stop / Reset Mode
Auto Mode
Alarm Mute & Lamp Test
Fault LED. Will be constant on warning
and flash upon Electrical Trip and Shutdown Fault
Close Generator
(Manual Mode Only)
Open Generator
Generator Breaker LED
Selected Mode Indication LED
Generator Available LED
Test Mode
Transfer to Generator
Transfer to Mains
Mains Breaker LED
Mains Available LED
4.3 CONTROL PUSH-BUTTONS
Icon Description
This button places the module into its Stop/Reset Mode . This clears any alarm conditions for which the triggering criteria have been removed. If the engine is running and the module is put into Stop mode, the module automatically instructs the generator to unload (Close Generator and Delayed Load Output 1, 2, 3 & 4 become inactive (if used)). The fuel supply de-energises and the engine comes to a standstill. Should any form of remote start signal be present when in Stop Mode the generator remains at rest
This button places the module into its Manual Mode . Once in
Manual Mode , the module responds to the Start button to start the generator and run it off load.
To place the generator on load, use the Transfer to Generator button. The module automatically instructs the changeover device to place the generator on load (Close Generator and Delayed Load Output 1, 2, 3 & 4 becomes active (if
used)). To place the generator off load, use the Transfer to Mains or Open Generator buttons. The module automatically instructs the changeover device to place the generator off load (Close Generator and Delayed Load Output 1, 2, 3 & 4 becomes inactive (if used)). Additional digital inputs can be assigned to perform these functions.
If the engine is running off-load in Manual Mode and a remote start signal becomes present, the module automatically instructs the changeover device to place the generator on load (Close Generator and Delayed Load Output 1, 2, 3 & 4 becomes active (if used)). Upon removal of the Remote Start Signal, the generator remains on load until either selection of the
Stop/Reset Mode or Auto Mode . For further details, please see section entitled Operation elsewhere in this manual.
Test Mode (DSE6020 MKII Only)
This button places the module into its Test Mode . Once in Test Mode , the
module responds to the Start button to start the generator and run it off load. Once the set has started the set automatically be placed on load (Close Generator and Delayed Load Output 1, 2, 3 & 4 become active in order from lowest to highest (if used)). For further details, please see section entitled Operation elsewhere in this manual.
This button places the module into its Auto Mode . This mode allows the module to control the function of the generator automatically. The module monitors the remote start input and once a start request is made, the set is automatically started and placed on load (Close Generator and Delayed Load Output 1, 2, 3 & 4 become active in order from lowest to highest (if used)). Upon removal of the starting signal, the module removes the load from the generator and shut the set down observing the stop delay timer and cooling timer as necessary (Close Generator and Delayed Load Output 1, 2, 3 & 4 become inactive at once (if used)). The module then waits for the next start event. For further details, please see section entitled Operation elsewhere in this manual.
Alarm Mute / Lamp Test This button de-activates the audible alarm output (if configured) and illuminates all of the LEDs on the modules facia.
This button is only active in the Stop/Reset Mode , Manual Mode and
Test Mode .
Pressing the Start button in Stop/Reset Mode powers up the ECU but does not start the engine. This can be used to check the status of the CAN communication and to prime the fuel system.
Pressing the Start button in Manual Mode or Test Mode starts the
generator and runs it off load in Manual Mode or on load in Test Mode .
Menu Navigation Used for navigating the instrumentation, event log and configuration screens. For further details, please see section entitled Operation elsewhere in this manual.
This button is only active in the Manual Mode and allows the operator to transfer the load to the generator.
Open Generator (DSE6010 MKII Only)
This button is only active in the Manual Mode and allows the operator to open the generator breaker and remove the load.
Transfer To Mains (DSE6020 MKII Only)
This button is only active in the Manual Mode and allows the operator to transfer the load to the mains.
4.4 MODULE DISPLAY The modules display contains the following sections.
NOTE: Depending upon the modules configuration, some display screens may be
disabled. For further details of module configuration, refer to DSE Publication: 057-223
Inst. Icon
Instrumentation Unit Alarm Icon
Active Config
Mode Icon
FPE / Auto Run
Example of DSE6010 MKII Home Page Display
L1N 230 V
230 V L1N 230 V
4.4.1 BACKLIGHT The LCD backlight is on if the unit has sufficient voltage while the unit is turned on, unless the unit is cranking for which the backlight is turned off.
4.4.2 INSTRUMENTATION ICONS When viewing instrumentation pages, an icon is displayed in the Inst. Icon section to indicate what section is currently being displayed.
Icon Details
/ The default home page which displays generator voltage and mains voltage (DSE6020 MKII only)
Generator voltage and frequency instrumentation screen
Mains voltage and frequency instrumentation screen (DSE6020 MKII only)
Generator current instrumentation screen
Mains current instrumentation screen (DSE6020 MKII only when CT in load location)
Load power instrumentation screen
Engine speed instrumentation screen
Hours run instrumentation screen
Battery voltage instrumentation screen
Oil pressure instrumentation screen
Coolant temperature instrumentation screen
Flexible sensor instrumentation screen
Appears when the event log is being displayed
Current time held in the unit
The current value of the scheduler run time and duration
ECU diagnostic trouble codes
Oil Filter maintenance timers
Air Filter maintenance timers
Fuel Filter maintenance timers
4.4.3 ACTIVE CONFIGURATION An icon is displayed in the Active Config section to indicate the active configuration within the currently selected within the controller.
Appears when the main configuration is selected.
Appears when the alternative configuration is selected.
4.4.4 FRONT PANEL EDITOR (FPE) / AUTO RUN ICON
NOTE: For further details about the Front Panel Editor, see the section entitled Front
Panel Editor elsewhere in this manual.
When running in Auto Mode and on the Home ( / ) page, an icon is displayed in the FPE / Auto Run section to indicate the source of the auto start signal.
Icon Auto Run Reason
Appears when a remote start input is active
Appears when a low battery run is active
Mains failure
Appears when a scheduled run is active
4.4.5 MODE ICON An icon is displayed in the Mode Icon section to indicate the mode the controller is currently in.
Appears when the engine is at rest and the unit is in Stop/Reset Mode .
Appears when the engine is at rest and the unit in Manual Mode .
Appears when the engine is at rest and the unit is Test Mode .
Appears when the engine is at rest and the unit is in Auto Mode .
Appears when a timer is active, for example cranking time, crank rest etc.
Appears when the engine is running, and all timers have expired, either on or off load. The animation speed is reduced when running in idle mode.
Appears when the unit is in the front panel editor.
Appears when a USB connection is made to the controller.
Appears if either the configuration file or engine file becomes corrupted.
4.4.6 ALARM ICONS (PROTECTIONS) An icon is displayed in the Alarm Icon section to indicate the alarm that is current active on the controller. In the event of a warning alarm, the LCD only displays the Alarm Icon. In the event of an electrical trip
or shutdown alarm, the module displays the Alarm Icon and the Stop/Reset Mode button LED begins to flash. If multiple alarms are active at the same time, the Alarm Icon automatically cycles through all the appropriate icons to indicate each alarm which is active.
Example: If the DSE controller was sensing a charge alternator failure alarm, delay over current alarm and a AC under voltage alarm at the same time, it would cycle through all of the icons to show this.
Icon cycle procedure
4.4.6.1 WARNING ALARM ICONS Warnings are non-critical alarm conditions and do not affect the operation of the generator system, they serve to draw the operators attention to an undesirable condition. By default, warning alarms are self-resetting when the fault condition is removed. However enabling all warnings are latched causes warning alarms to latch until reset manually. This is enabled using the DSE Configuration Suite in conjunction with a compatible PC.
Icon Fault Description
Auxiliary Inputs
The module detects that an auxiliary input which has been user configured to create a fault condition has become active.
Analogue Input
The module detects that an input configured to create a fault condition has become active.
Fail To Stop
NOTE: Fail to Stop could indicate a faulty oil pressure
sensor. If engine is at rest check oil sensor wiring and
configuration.
The module has detected a condition that indicates that the engine is running when it has been instructed to stop.
Charge Failure
The auxiliary charge alternator voltage is low as measured from the W/L terminal.
The level detected by the fuel level sensor is below the low fuel level pre-set pre-alarm setting.
High Fuel Level
The level detected by the fuel level sensor is above the high fuel level pre-set pre-alarm setting.
Battery Under Voltage
The DC supply has fallen below or risen above the low volts pre-set pre-alarm setting.
Battery Over Voltage
The DC supply has risen above the high volts pre-set pre-alarm setting.
Generator Under Voltage
The generator output voltage has fallen below the pre-set pre-alarm setting after the Safety On timer has expired.
Generator Over Voltage
The generator output voltage has risen above the pre-set pre-alarm setting.
Generator Under Frequency
The generator output frequency has fallen below the pre-set pre-alarm setting after the Safety On timer has expired.
Generator Over Frequency
The generator output frequency has risen above the pre-set pre-alarm setting.
CAN ECU Fault The engine ECU has detected an alarm
CAN Data Fail
The module is configured for CAN operation and does not detect data on the engine Can data link.
Immediate Over Current
The measured current has risen above the configured trip level.
Delayed Over Current
The measured current has risen above the configured trip level for a configured duration.
Oil Filter Maintenance Alarm
Maintenance due for oil filter.
Air Filter Maintenance Alarm
Maintenance due for air filter
Fuel Filter Maintenance Alarm
Maintenance due for fuel filter.
4.4.6.2 ELECTRICAL TRIP ALARM ICONS
NOTE: The alarm condition must be rectified before a reset takes place. If the alarm
condition remains, it is not possible to reset the unit (The exception to this is the Low Oil
Pressure alarm and similar active from safety on alarms, as the oil pressure is low with the
engine at rest).
Electrical trips are latching and stop the Generator but in a controlled manner. On initiation of the electrical trip condition the module de-energises all the Delayed Load Output and the Close Gen Output outputs to remove the load from the generator. Once this has occurred the module starts the Cooling timer and allows the engine to cool off-load before shutting down the engine. The alarm must be accepted and cleared, and the fault removed to reset the module.
Electrical trips are latching alarms and to remove the fault, press the Stop/Reset Mode button on the module.
The level detected by the fuel level sensor is below the low fuel level pre-set alarm setting.
The level detected by the fuel level sensor is above the high fuel level pre-set alarm setting.
kW Overload
The measured kW has risen above the configured trip level for a configured duration.
4.4.6.3 SHUTDOWN ALARM ICONS
condition remains, it is not be possible to reset the unit (The exception to this is the Low Oil
Shutdown alarms are latching and immediately stop the Generator. On initiation of the shutdown condition the module de-energises all the Delayed Load Output and the Close Gen Output outputs to remove the load from the generator. Once this has occurred, the module shuts the generator set down immediately to prevent further damage. The alarm must be accepted and cleared, and the fault removed to reset the module.
Shutdowns are latching alarms and to remove the fault, press the Stop/Reset Mode button on the module.
Fail To Start
The engine has failed to start after the configured number of start attempts
Low Oil Pressure
The module detects that the engine oil pressure has fallen below the low oil pressure pre-alarm setting level after the Safety On timer has expired.
Engine High Temperature
The module detects that the engine coolant temperature has exceeded the high engine temperature pre-alarm setting level after the Safety On timer has expired.
Under Speed
The engine speed has fallen below the under speed pre alarm setting
Over Speed The engine speed has risen above the over speed pre alarm setting
The generator output voltage has fallen below the pre-set alarm setting. after the Safety On timer has expired.
The generator output voltage has risen above the pre-set alarm setting.
Additional shutdown alarm icons can be viewed overleaf.
The generator output frequency has fallen below the pre-set alarm setting after the Safety On timer has expired.
The generator output frequency has risen above the pre-set alarm setting.
CAN ECU Fault
The engine ECU has detected an alarm CHECK ENGINE LIGHT Contact Engine Manufacturer for support.
Emergency Stop
The emergency stop button has been depressed. This failsafe (normally closed to emergency stop) input and immediately stops the set should the signal be removed.
Oil Sender Open Circuit
The oil pressure sensor has been detected as being open circuit.
Coolant Temperature Sender Open Circuit
The coolant temperature sensor has been detected as being open circuit.
4.5 VIEWING THE INSTRUMENT PAGES
4.5.1 NAVIGATION MENU
To enter the navigation menu, press both the (up) and (down) buttons simultaneously.
To select the required icon, press the (up) button to cycle right or the (down) button to cycle left until the desired instrumentation section is reached.
Once the desired icon is at the top, press the Auto Mode () button to enter that instrunmentation section.
If the Auto Mode () button is not pressed, the display automatically returns to the Home ( / ) page after the configured setting of the LCD Scroll Timer.
4.5.1.1 NAVIGATION MENU ICONS
Generator and mains voltage instrumentation (DSE6020 MKII only)
/ Generator instrumentation
Mains instrumentation (DSE6020 MKII only)
Current and load instrumentation
Engine instrumentation
Engine DTCs (Diagnostic Trouble Codes) i
DSE6010 MKII DSE6020 MKII Installation Instructions
CS-1000RGB MKII CS-2000RGB MKII - Get in the Miximages.getinthemix.com/resources/1462783952_0321.pdf · CS-1000RGB MKII CS-2000RGB MKII Please spend a few minutes to read this manual
OWNER'S MANUAL B15, B30, B100 MKII, B200 MKII, B450 MKII
DSE6110 MKII & DSE6120 MKII Operator Manual...057-236 ISSUE: 1 DEEP SEA ELECTRONICS PLC DSE6110 MKII & DSE6120 MKII Operator Manual Document Number: 057-236 Author: Mark GrahamDSE6110
DSE Genset DSE 6010/20 MKII - storage.googleapis.comstorage.googleapis.com/.../DSE6010-MKII-DSE6020-MKII-Data-Sheet-(… · dse genset ® dse 6010/20 mkii auto start and auto mains
Dse7110 Mkii Dse7120 Mkii Operator Manual
DEEP SEA ELECTRONICSplantaselectricasdemexico.com/...MKII-DSE7320-MKII... · DSE7310 MKII & DSE7320 MKII Configuration Suite PC Software Manual Document Number: 057-243 Author: Fady
Dse6010 20 Manual
Density MkII Manual
DSE7410 MKII & DSE7420 MKII Operator Manual Document ... · 057-263 ISSUE: 1 DEEP SEA ELECTRONICS PLC DSE7410 MKII & DSE7420 MKII Operator Manual Document Number: 057-263 Author:
Editorial MkII
Warmachine MKII
Claplight MKII
MKII Device Supplement - zetaalarmsystems.com512 Fyreye MKII Fixed Temperature Heat Detector MKII-AHF 0.5 N/A 5 250 512 Fyreye MKII Addressable Opto-Heat Detector MKII-AOH 0.5 N/A
MKII - UNOLS
DEEP SEA ELECTRONICS 053-148 ISSUE 1 DSE892 …setecom.com/wp-content/uploads/2015/09/DSE892-Data-Sheet-USA.pdf · 4 INSTALLATION ... 057-223 DSE6010 MKII & DSE6020 MKII Configuration
DSE7410 MKII & DSE7420 MKII Configuration Suite PC
Viking 5.2 MKII
MKII Device Supplement - Zeta Alarm Systems · 512 Sounders & Flashers Fyreye MKII Addressable Maxitone Sounder MKII-AMT 0.65 N/A 7 32 128 Fyreye MKII Addressable Maxitone Sounder
C3 MKII Manual
Old Lady MkII
DSE6010 MKII & DSE6020 MKII Operator Manual · 2020-03-11 · Introduction Page 7 of 100 057-230 ISSUE: 1 1 INTRODUCTION This document details the installation and operation requirements
Arturia - MiniLab mkII - Englishdownloads.arturia.com/.../minilab-mkII/manual/MiniLabmkII_Manual_1... · 4 ARTURIA – MiniLab mkII– USER'S MANUAL v1.0 Speecciaall MMeessssaagge
パゴデ MkII ラックシステム - AXISSパゴデMkII ラックシステム フィニッテ・エレメンテを代表する"PAGODE MkII" (パゴデMkII)ラックシステム。
DSE6110 MKII / DSE6120 MKII Configuration Suite PC ... · PDF fileDSE6110 MKII / DSE6120 MKII Configuration Suite PC Software Manual Page 3 of 104 057-224 ISSUE: 2 TABLE OF CONTENTS
RX-178 MKII
Thorens Td166 Mkii
AVR Prog MKII - And-Techand-tech.pl/wp-content/download/avrprog mkii/avr prog mkii v1.0_eng... · To configure AVR Prog MKII, please start AVR Studio. Programmer's options are available
DSE7310 MKII & DSE7320 MKII Software Manual
Ambassador class MKII